| ||Format||Pages||Price|| |
|12||$56.00||  ADD TO CART|
|Hardcopy (shipping and handling)||12||$56.00||  ADD TO CART|
|Standard + Redline PDF Bundle||24||$67.00||  ADD TO CART|
Significance and Use
5.1 This test method is used to determine the time to sustained flaming and heat release of materials and composites exposed to a prescribed initial test heat flux in the cone calorimeter apparatus.
5.2 Quantitative heat release measurements provide information that can be used to compare wall or ceiling coverings and constructions and for input to fire models.
5.3 Heat release measurements provide useful information for product development by giving a quantitative measure of specific changes in fire performance caused by component and composite modifications.
5.4 Heat release data obtained by this test method will be inappropriate if the product will not spread flame over its surface under the fire exposure conditions of interest.
5.5 Variations in substrates, mounting methods, and adhesives used to laminate composite products will potentially affect the test responses. These variables must be controlled during any comparative experiments.
5.6 Test Limitations—The test data are invalid if any of the following occur:
5.6.1 Explosive spalling,
5.6.2 The specimen swells sufficiently prior to ignition to touch the spark plug or swells up to the plane of the heater base during combustion, or
5.6.3 The surface laminate rolls or curls when placed under the radiant heater.
5.7 The specimens are subjected to one or more specific sets of laboratory conditions in this procedure. If different test conditions are substituted or the end-use conditions are changed, it is not always possible by or from this test to predict changes in the fire-test-response characteristics measured. The results are therefore valid only for the fire test exposure conditions described in this procedure.
1.1 This fire-test-response test method covers determination of the ignitability and heat release rate of composites consisting of a wall covering or ceiling covering, a substrate, and all laminating adhesives, coatings, and finishes. Heat release information cannot be used alone to evaluate the flammability of wall coverings or ceiling coverings. The data are intended to be used for modeling or with other data to evaluate a material.
1.2 This test method provides for measurement of the time to sustained flaming, heat release rate, peak and total heat release, and effective heat of combustion at a constant initial test heat flux of 35 kW/m2. Heat release data at different heat fluxes are also obtained by this test method. The specimen is oriented horizontally, and a spark ignition source is used.
1.3 The fire-test-response characteristics are determined using the apparatus and procedures described in Test Method .
1.4 The tests are conducted on bench-scale specimens combining the components used in the actual installation.
1.5 The values stated in SI units are to be regarded as the standard. See .
1.6 Fire testing of products and materials is inherently hazardous, and adequate safeguards for personnel and property shall be used in conducting these tests. This test method potentially involves hazardous materials, operations, and equipment.
1.7 This standard is used to measure and describe the response of materials, products, or assemblies to heat and flame under controlled conditions, but does not by itself incorporate all factors required for fire hazard or fire risk assessment of the materials, products, or assemblies under actual fire conditions.
1.8 Fire testing is inherently hazardous. Adequate safeguards for personnel and property shall be employed in conducting these tests. Specific information about hazard is given in Section .
1.9 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.
1.10 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C1186 Specification for Flat Fiber-Cement Sheets
D123 Terminology Relating to Textiles
D5865 Test Method for Gross Calorific Value of Coal and Coke
E84 Test Method for Surface Burning Characteristics of Building Materials
E176 Terminology of Fire Standards
E603 Guide for Room Fire Experiments
E906 Test Method for Heat and Visible Smoke Release Rates for Materials and Products Using a Thermopile Method
E1354 Test Method for Heat and Visible Smoke Release Rates for Materials and Products Using an Oxygen Consumption Calorimeter
E1474 Test Method for Determining the Heat Release Rate of Upholstered Furniture and Mattress Components or Composites Using a Bench Scale Oxygen Consumption Calorimeter
NFPA StandardNFPA 265 Standard Methods of Fire Tests for Evaluating Room Fire Growth Contribution of Textile Wall Covering
ICS Number Code 13.220.50 (Fire-resistance of building materials and elements)
UNSPSC Code 30161500(Wall finishing materials)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM E1740-20, Standard Test Method for Determining the Heat Release Rate and Other Fire-Test-Response Characteristics of Wall Covering or Ceiling Covering Composites Using a Cone Calorimeter, ASTM International, West Conshohocken, PA, 2020, www.astm.orgBack to Top