| ||Format||Pages||Price|| |
|8||$43.00||  ADD TO CART|
|Hardcopy (shipping and handling)||8||$43.00||  ADD TO CART|
|Standard + Redline PDF Bundle||16||$51.60||  ADD TO CART|
This specification covers the in-service care, inspection, testing, and use voltage of insulating gloves and sleeves for protection from electrical shock. Gloves and sleeves covered under this specification are designated as type I or type II; class 00, class 0, class 1, class 2, class 3, or class 4. Type I - nonresistant to ozone, made from a high-grade cis-1,4-polyisoprene rubber compound of natural or synthetic origin, properly vulcanized, and type II - ozone resistant, made of any elastomer or combination of elastomeric compounds. The recommended sequence of inspection and testing of gloves and sleeves at an electrical testing facility are: check-in, washing, and preliminary inspection; repair; electrical test; drying; final inspection; record-keeping and marking; and powdering, pairing, and packing for storage or shipment. Electrical testing shall be performed to meet the requirements prescribed.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers the in-service care, inspection, testing, and use voltage of insulating gloves and sleeves for protection from electrical shock.
1.2 The values stated in SI units are to be regarded as the standard. See IEEE/ASTM SI-10.
1.3 The following safety hazards caveat pertains only to the test method portion, Sections and , of this specification. This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. For a specific warning statement, see .
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
ANSI StandardsC 39.5 Safety Requirements for Electrical and Electronic Measuring and Controlling Instrumentation Available from American National Standards Institute (ANSI), 25 W. 43rd St., 4th Floor, New York, NY 10036, http://www.ansi.org.
D120 Specification for Rubber Insulating Gloves
D1051 Specification for Rubber Insulating Sleeves
D2865 Practice for Calibration of Standards and Equipment for Electrical Insulating Materials Testing
F696 Specification for Leather Protectors for Rubber Insulating Gloves and Mittens
F819 Terminology Relating to Electrical Protective Equipment for Workers
F1236 Guide for Visual Inspection of Electrical Protective Rubber Products
ICS Number Code 13.260 (Protection against electric shock. Live working)
UNSPSC Code 46181537(Insulated gloves); 46181516(Safety sleeves)
ASTM F496-14a, Standard Specification for In-Service Care of Insulating Gloves and Sleeves, ASTM International, West Conshohocken, PA, 2014, www.astm.orgBack to Top