Significance and Use
3.1 The dielectric breakdown voltage of an insulating liquid is of importance as a measure of the liquid's ability to withstand electric stress without failure. The dielectric breakdown voltage serves to indicate the presence of contaminating agents such as water, dirt, cellulosic fibers, or conducting particles in the liquid, one or more of which may be present in significant concentrations when low breakdown voltages are obtained. However, a high dielectric breakdown voltage does not necessarily indicate the absence of all contaminants; it may merely indicate that the concentrations of contaminants that are present in the liquid between the electrodes are not large enough to deleteriously affect the average breakdown voltage of the liquid when tested by this test method (see Appendix X1.)
3.2 This test method is used in laboratory or field tests. For field breakdown results to be comparable to laboratory results, all criteria including room temperature (20 to 30°C) must be met.
1.1 This test method covers the determination of the dielectric breakdown voltage of insulating liquids (oils of petroleum origin, silicone fluids, high fire-point mineral electrical insulating oils, synthetic ester fluids and natural ester fluids). This test method is applicable to insulating liquids commonly used in cables, transformers, oil circuit breakers, and similar apparatus as an insulating and cooling medium. Refer to Terminology D2864 for definitions used in this test method.
1.2 This test method is sensitive to the deleterious effects of moisture in solution especially when cellulosic fibers are present in the liquid. It has been found to be especially useful in diagnostic and laboratory investigations of the dielectric breakdown strength of insulating liquid in insulating systems.
1.3 This test method is used to judge if the VDE electrode breakdown voltage requirements are met for insulating liquids. This test method should be used as recommended by professional organization standards such as IEEE C57.106.
1.4 This test method may be used to obtain the dielectric breakdown of silicone fluid as specified in Test Method D2225 and Specification D4652, provided that the discharge energy into the sample is less than 20 mJ (milli joule) per breakdown for five consecutive breakdowns.
1.5 Both the metric and the alternative inch-pound units are acceptable.
1.6 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D235 Specification for Mineral Spirits (Petroleum Spirits) (Hydrocarbon Dry Cleaning Solvent)
D923 Practices for Sampling Electrical Insulating Liquids
D2225 Test Methods for Silicone Fluids Used for Electrical Insulation
D2864 Terminology Relating to Electrical Insulating Liquids and Gases
D3487 Specification for Mineral Insulating Oil Used in Electrical Apparatus
D4652 Specification for Silicone Fluid Used for Electrical Insulation
D6871 Specification for Natural (Vegetable Oil) Ester Fluids Used in Electrical Apparatus
C57.106 Guide for Acceptance and Maintenance of Insulating Oil in Equipment
breakdown voltage; dielectric strength; insulating liquids; insulating oils; test cell; VDE electrodes;
ICS Number Code 29.040.10 (Insulating oils)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]