This specification covers carbon steel pipe for high-temperature service. These pipes are suitable for welding, bending, flanging, and similar forming operations. Mechanical testing of the specimens shall include tensile, bending, flattening, hydrostatic and nondestructive electric tests. Specimens undergoing bending tests shall consist of sections cut from a pipe. For flattening tests, the specimens shall be smooth on the ends and burr-free, except when made on crop ends. All tests shall be performed in room temperature. If any test specimen shows flaws it can be discarded and substituted for another test specimen. Before testing, if a specimen has scribe scratches, a retest shall be allowed. A retest shall also be allowed if a specimen breaks in an inside or outside surface flaw.
1.1 This specification covers seamless carbon steel pipe for high-temperature service ( ) in NPS 1/8 to NPS 48 [DN 6 to DN 1200] ( ) inclusive, with nominal (average) wall thickness as given in ASME B 36.10M. It shall be permissible to furnish pipe having other dimensions provided such pipe complies with all other requirements of this specification. Pipe ordered under this specification shall be suitable for bending, flanging, and similar forming operations, and for welding. When the steel is to be welded, it is presupposed that a welding procedure suitable to the grade of steel and intended use or service will be utilized.
Note 1: It is suggested, consideration be given to possible graphitization.
Note 2: The dimensionless designator NPS (nominal pipe size) [DN (diameter nominal)] has been substituted in this standard for such traditional terms as “nominal diameter,” “size,” and “nominal size.”
1.2 Supplementary requirements of an optional nature are provided for seamless pipe intended for use in applications where a superior grade of pipe is required. These supplementary requirements call for additional tests to be made and when desired shall be so stated in the order.
1.3 The values stated in either SI units or inch-pound units are to be regarded separately as standard. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in non-conformance with the standard.
1.4 The following precautionary caveat pertains only to the test method portion, Sections This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use. , , and of this specification:
1.5 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.