| ||Format||Pages||Price|| |
|5||$52.00||  ADD TO CART|
|Hardcopy (shipping and handling)||5||$52.00||  ADD TO CART|
Significance and Use
5.1 This practice is suitable for the removal of contaminants found on materials, parts, and components used in systems requiring a high level of cleanliness, such as oxygen. Parts shall have been precleaned to remove visible contaminants prior to using this procedure. Softgoods such as seals and valve seats may be cleaned without precleaning.
5.2 This procedure may also be used as the cleanliness verification technique for coupons used during cleaning effectiveness tests as in Test Method .
5.3 The cleaning efficiency has been shown to vary with the frequency and power density of the ultrasonic unit. Low frequencies in the 20 to 25 kilohertz range have been found to damage soft metals such as aluminum and silver. Therefore, the specifications of the unit and the frequencies available must be considered in order to optimize the cleaning conditions without damaging the parts.
1.1 This practice covers a procedure for the cleaning of materials and components used in systems requiring a high level of cleanliness, such as oxygen, by ultrasonic techniques.
1.2 This practice may be used for cleaning small parts, components, softgoods, etc.
1.3 The values stated in SI units are standard.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Specific precautionary statements are given in .
1.5 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1193 Specification for Reagent Water
E1235 Test Method for Gravimetric Determination of Nonvolatile Residue (NVR) in Environmentally Controlled Areas for Spacecraft
F311 Practice for Processing Aerospace Liquid Samples for Particulate Contamination Analysis Using Membrane Filters
F324 Test Method for Nonvolatile Residue of Volatile Cleaning Solvents Using the Solvent Purity Meter
F331 Test Method for Nonvolatile Residue of Solvent Extract from Aerospace Components (Using Flash Evaporator)
G121 Practice for Preparation of Contaminated Test Coupons for the Evaluation of Cleaning Agents
G122 Test Method for Evaluating the Effectiveness of Cleaning Agents
ICS Number Code 03.080.10 (Industrial services)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM G131-96(2016)e1, Standard Practice for Cleaning of Materials and Components by Ultrasonic Techniques, ASTM International, West Conshohocken, PA, 2016, www.astm.orgBack to Top