| ||Format||Pages||Price|| |
|8||$54.00||  ADD TO CART|
|Hardcopy (shipping and handling)||8||$54.00||  ADD TO CART|
|Standard + Redline PDF Bundle||16||$64.00||  ADD TO CART|
1.1 This specification establishes performance requirements for flame mitigation devices (FMDs) in portable fuel containers (PFCs) for gasoline, kerosene, and diesel fuels intended for reuse by the consumer.
1.2 A flame mitigation device in gasoline (red), diesel (yellow), and kerosene (blue) PFCs protects the container openings from possible propagation of a flame into a flammable fuel-air mixture within the container. Formation of a flammable fuel-air mixture in the container can occur in special circumstances associated with cold ambient conditions and low liquid levels in the container. Delineations of those circumstances and conditions have been described in published reports, for example, Gardiner et al, 2010 (), and papers, for example, Elias et al, 2013 (), including research sponsored and overseen by the ASTM F15.10 Technical Committee.
1.3 This specification does not address the hazard of injury or death caused by ignition of vapors external to the PFC when the fuel in the PFC is poured onto or near to a fire or other ignition source causing these external vapors to ignite or explode. An FMD does not prevent hazards associated with misuse of the PFC resulting in external vapor ignition.
1.4 The flame mitigation device is chemically conditioned by exposure to representative fuel surrogates CE25a and CE85a fuel and other expected conditions prior to the tests.
1.5 The flame mitigation device is mechanically conditioned by repeated insertions and removal of a fuel refueling spout prior to the tests.
1.6 The first test method establishes that the flame mitigation device can effectively prevent flame propagation into a flammable butane-air mixture inside the portable fuel container. The butane-air mixture is a controlled and repeatable proxy for the more variable fuel vapor-air mixture in the container.
1.7 The second test method establishes that the flame mitigation device is permitting adequate flow rates of fuel.
1.8 This specification states values in SI units which are to be regarded as the standard. The values given in parentheses are for information only.
1.9 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.
1.10 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
Other StandardsNFPA 497 Recommended Practice for the Classification of Flammable Liquids, Gases, or Vapors of Hazardous (Classified) Locations for Electrical Installations in Chemical Process Areas Available from National Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy, MA 02169-7471, http://www.nfpa.org.
F852 Specification for Portable Gasoline, Kerosene, and Diesel Containers for Consumer Use
ICS Number Code 55.140 (Barrels. Drums. Canisters)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F3326-21, Standard Specification for Flame Mitigation Devices on Portable Fuel Containers, ASTM International, West Conshohocken, PA, 2021, www.astm.orgBack to Top