| ||Format||Pages||Price|| |
|2||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||2||$44.00||  ADD TO CART|
Significance and Use
4.1 The ATL value is used to set the break-away strength of a weak-link device, or to set other equipment used to limit pulling force during pull-in installation of polyethylene gas pipe, or to determine if pulling equipment can extert pulling force greater than the ATL value for the polyethylene gas pipe being installed.
4.2 The ATL value is determined before gas pipe installation.
1.1 This practice provides a means to determine an allowable tensile load (ATL) value for a polyethylene gas pipe that is to be installed underground using methods that pull the pipe into a trench (cut or plowed), bore hole, casing pipe, or the like. The ATL value takes into account pipe size, tensile yeild strength, pipe temperature, and pulling load duration.
1.2 The ATL is used to set the break-away strength for a “weak-link” device, or as a limit setting for other devices that control the maximum pulling force exerted by equipment used to pull polyethylene gas pipe into an underground location, or to determine if pulling equipment can extert pulling force greater than the ATL value for the gas pipe being installed. A weak-link device is installed where the pipe pulling equipment is connected to the polyethylene gas pipe. If pulling load exceeds the ATL limit, the device de-couples the pipe from the pulling equipment. Other measures or equipment that limit the pulling force on the pipe are also used. When the ATL value is compared to the pulling force developed by the pull-in installation equipment and equipment cannot extert pulling force greater than the ATL value, a weak-link or other device for limiting the pulling force is not necessary.
1.3 This practice does not address weak-link device design or requirements, nor does it address the design or requirements for other equipment or procedures used to limit the pulling force applied to polyethylene gas pipe during pull-in installation.
1.4 This practice does not address installation methods or procedures employed for pull-in of polyethylene gas pipe.
1.5 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.6 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D638 Test Method for Tensile Properties of Plastics
D1600 Terminology for Abbreviated Terms Relating to Plastics
D2513 Specification for Polyethylene (PE) Gas Pressure Pipe, Tubing, and Fittings
F412 Terminology Relating to Plastic Piping Systems
ICS Number Code 23.040.20 (Plastic pipes)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F1804-08(2016), Standard Practice for Determining Allowable Tensile Load for Polyethylene (PE) Gas Pipe During Pull-In Installation, ASTM International, West Conshohocken, PA, 2016, www.astm.orgBack to Top