| ||Format||Pages||Price|| |
|6||$45.00||  ADD TO CART|
|Hardcopy (shipping and handling)||6||$45.00||  ADD TO CART|
Significance and Use
This test method is a standard procedure for determining the air leakage characteristics of installed exterior windows and doors under specified static air pressure differences.
Note 1—The air pressure differences acting across a building envelope vary greatly. The factors affecting air pressure differences and the implications of the resulting air leakage relative to the environment within buildings are discussed in the literature. , , These factors should be fully considered in specifying the test pressure differences to be used.
Rates of air leakage are sometimes used for comparison purposes. Such comparisons may not be valid unless the components being tested and compared are of essentially the same size, configuration, and design.
Rates of air leakage of essentially identical windows or doors, as determined in the laboratory (Test Method E283) and as measured in the field by this test method, have sometimes been used for comparison purposes. The correlation between the laboratory and field test results, and the correlation between actual performance of in-service products and the response to these tests has not been established because of insufficient data.
Rates of air leakage, as determined by this test method may be affected by: the age or physical condition of the test specimen; the type or quality of installation; the care exercised in the attachment of the test apparatus and the determination of extraneous leakage; and the actual conditions to which the test specimen is exposed beyond those imposed by the test method, that is temperature, relative humidity, wind impingement, etc. Consideration must be given to the proper selection of test specimens, the choice of appropriate test technique (when a choice is given within this test method), and the proper use and interpretation of the results obtained from this test to minimize the effect of these conditions.
Rates of air leakage, as determined by this test method may include air leakage that does not occur during normal operation and exposure, or that does not contribute to the overall air leakage for the structure. Air may be supplied to or exhausted from wall cavities or adjacent construction, or may bypass interior or exterior trim or components in a manner not experienced during normal operation or exposure. Care must be taken to prevent such leakage from occurring, or consideration must be given that such leakage may have occurred during the test.
This test method addresses the issue of air leakage through the high pressure face of the test specimen only. Air leakage from the adjacent wall cavity through sill, head, and jambs of the window frame is considered extraneous air leakage and, therefore, not a component of the measured specimen air leakage. Such extraneous air leakage through the perimeter frame of the test specimen can be a significant source of air leakage into, or out of, the building if the frame is not sealed against air infiltration from the adjacent wall cavity.
1.1 This test method provides a field procedure for determining the air leakage rates of installed exterior windows and doors.
1.2 This test method is applicable to exterior windows and doors and is intended to measure only such leakage associated with the assembly and not the leakage through openings between the assemblies and adjacent construction. The test method can be adapted for the latter purpose, provided the potential paths of air movement and the sources of infiltration and exfiltration can be identified, controlled, or eliminated.
1.3 This test method attempts to create and given set of natural environmental conditions. There is a strong possibility that the test method or the test apparatus may, by virtue of their design and use, induce air leakage that does not occur under natural environmental exposure.
1.4 This test method is intended for the field testing of installed exterior windows or doors. Persons interested in laboratory testing of fenestration products should reference Test Method E283.
1.5 Persons using this procedure should be knowledgeable in the area of fluid mechanics and instrumentation practices, and shall have a general understanding of fenestration products and components.
1.6 The values stated in SI units are to be regarded as standard. The values given in parentheses are mathematical conversions to inch-pound units that are provided for information only and are not considered standard.
1.7 This standard does not purport to address all of the safety problems, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. For specific precautionary statements, see Section 7.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
E283 Test Method for Determining Rate of Air Leakage Through Exterior Windows, Curtain Walls, and Doors Under Specified Pressure Differences Across the Specimen
E631 Terminology of Building Constructions
ICS Number Code 91.060.50 (Doors and windows)
UNSPSC Code 30170000(Doors and windows and glass)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM E783-02(2010), Standard Test Method for Field Measurement of Air Leakage Through Installed Exterior Windows and Doors, ASTM International, West Conshohocken, PA, 2010, www.astm.orgBack to Top