| ||Format||Pages||Price|| |
|14||$52.00||  ADD TO CART|
|Hardcopy (shipping and handling)||14||$52.00||  ADD TO CART|
Significance and Use
5.1 This test method evaluates the ability of exterior vents that mount vertically or horizontally to resist the entry of embers and flame penetration through the vent.
5.2 Flame Intrusion Test—Refer to the Significant and Use Section in Test Method E2912 for information related to the direct flame impingement on the vent.
1.1 This fire-test-response standard prescribes two individual methods to evaluate the ability of a gable end, crawl space (foundation) and other vents that mount on a vertical wall or in the under-eave area to resist the entry through the vent opening of embers and flame. The ability of such vents to completely exclude entry of flames or embers is not evaluated. Roof ridge and off-ridge (field) vents are excluded from this standard. Acceptance criteria are not provided in this standard.
1.2 Ember entry and flame penetration are evaluated separately using different test procedures. A commentary and summary of the development of the ember test apparatus are given in Appendix X1.
1.3 These laboratory tests are used to evaluate the response of vents when subjected to ember and flame exposures under controlled conditions.
1.4 Units—The values stated in either SI units or inch-pound units are to be regarded separately as standard. The values stated in each system are not necessarily exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems has the potential to result in non-conformance with the standard.
1.5 Unless otherwise specified, the tolerance for dimensions in figures and text in this document shall be ±5 %.
1.6 This test method does not address interior fire spread.
1.7 The standard is used to measure and describe the response of materials, products or assemblies to heat and flame under controlled conditions, but does not by itself incorporate all factors required for fire hazard or fire risk assessments of the materials, products or assemblies and other cladding materials under actual fire conditions.
1.8 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
1.9 Fire testing is inherently hazardous. Adequate safeguards for personnel and property shall be employed in conducting these tests.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1929 Test Method for Determining Ignition Temperature of Plastics
E108 Test Methods for Fire Tests of Roof Coverings
E176 Terminology of Fire Standards
E2257 Test Method for Room Fire Test of Wall and Ceiling Materials and Assemblies
E2707 Test Method for Determining Fire Penetration of Exterior Wall Assemblies Using a Direct Flame Impingement Exposure
E2912 Test Method for Fire Test of Non-Mechanical Fire Dampers Used in Vented Construction
ICS Number Code 13.220.99 (Other standards related to fire protection); 91.140.30 (Ventilation and air-conditioning systems)
UNSPSC Code 40101503(Vents)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM E2886 / E2886M-14, Standard Test Method for Evaluating the Ability of Exterior Vents to Resist the Entry of Embers and Direct Flame Impingement, ASTM International, West Conshohocken, PA, 2014, www.astm.orgBack to Top