| ||Format||Pages||Price|| |
|4||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$44.00||  ADD TO CART|
Significance and Use
5.1 This practice is intended for use by the material specifier, general contractor, applicator, or any individual group requiring information regarding the application of SFRM.
5.2 This practice is not intended to replace the manufacturers' application instructions.
1.1 This practice covers guidelines for application of sprayed fiber and cementitious fire-resistive materials.
1.2 This practice is general in nature. It is not intended to cover all requirements for application.
1.3 The values stated in either SI units or inch-pound units are to be regarded separately as standard. The values stated in each system are not necessarily exact equivalents; therefore, to ensure conformance with the standard, each system shall be used independently of the other, and values from the two systems shall not be combined.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use. Specific precautionary statements are given in Section and .
1.5 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
E119 Test Methods for Fire Tests of Building Construction and Materials
E605/E605M Test Methods for Thickness and Density of Sprayed Fire-Resistive Material (SFRM) Applied to Structural Members
E631 Terminology of Building Constructions
E736/E736M Test Method for Cohesion/Adhesion of Sprayed Fire-Resistive Materials Applied to Structural Members
E759/E759M Test Method for Effect of Deflection on Sprayed Fire-Resistive Material Applied to Structural Members
E760/E760M Test Method for Effect of Impact on Bonding of Sprayed Fire-Resistive Material Applied to Structural Members
E1368 Practice for Visual Inspection of Asbestos Abatement Projects
ICS Number Code 13.220.20 (Fire protection)
UNSPSC Code 30141605(Fireproofing material)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM E1513 / E1513M-93(2020), Standard Practice for Application of Sprayed Fire-Resistive Materials (SFRMs), ASTM International, West Conshohocken, PA, 2020, www.astm.orgBack to Top