| ||Format||Pages||Price|| |
|13||$56.00||  ADD TO CART|
|Hardcopy (shipping and handling)||13||$56.00||  ADD TO CART|
Significance and Use
4.1 This guide outlines the requirements for monitoring the performance of in-service fire-resistant fluids based on triaryl phosphate esters to accomplish safe and reliable operation of turbine electro-hydraulic control systems.
1.1 This guide provides recommendations to achieve safe and reliable operation of EHC systems, recommended levels for required corrective action, and suggested management practices.
1.2 The recommended set of physical and chemical properties of triaryl phosphate esters and their limits have been selected based on past operating experience with various fluids (primarily xylylated and butylated triaryl phosphate esters) used in different EHC system designs under different operating and environmental conditions.
1.3 This guide is not intended to replace Original Equipment Manufacturer (OEM) specifications but rather support users experiencing operating problems by recommending limits based on existing knowledge of triaryl phosphate ester degradation mechanisms. This guide should be used outside the warranty period or in cases where no OEM standard exists or is available.
1.4 The values stated in SI units are to be regarded as standard. No other units of measurement are included in this standard.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.
1.6 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D445 Test Method for Kinematic Viscosity of Transparent and Opaque Liquids (and Calculation of Dynamic Viscosity)
D664 Test Method for Acid Number of Petroleum Products by Potentiometric Titration
D892 Test Method for Foaming Characteristics of Lubricating Oils
D974 Test Method for Acid and Base Number by Color-Indicator Titration
D1169 Test Method for Specific Resistance (Resistivity) of Electrical Insulating Liquids
D1298 Test Method for Density, Relative Density, or API Gravity of Crude Petroleum and Liquid Petroleum Products by Hydrometer Method
D1500 Test Method for ASTM Color of Petroleum Products (ASTM Color Scale)
D3427 Test Method for Air Release Properties of Hydrocarbon Based Oils
D4052 Test Method for Density, Relative Density, and API Gravity of Liquids by Digital Density Meter
D4057 Practice for Manual Sampling of Petroleum and Petroleum Products
D4175 Terminology Relating to Petroleum Products, Liquid Fuels, and Lubricants
D4293 Specification for Phosphate Ester Based Fluids for Turbine Lubrication and Steam Turbine Electro-Hydraulic Control (EHC) Applications
D4898 Test Method for Insoluble Contamination of Hydraulic Fluids by Gravimetric Analysis
D5185 Test Method for Multielement Determination of Used and Unused Lubricating Oils and Base Oils by Inductively Coupled Plasma Atomic Emission Spectrometry (ICP-AES)
D6224 Practice for In-Service Monitoring of Lubricating Oil for Auxiliary Power Plant Equipment
D6304 Test Method for Determination of Water in Petroleum Products, Lubricating Oils, and Additives by Coulometric Karl Fischer Titration
D6595 Test Method for Determination of Wear Metals and Contaminants in Used Lubricating Oils or Used Hydraulic Fluids by Rotating Disc Electrode Atomic Emission Spectrometry
D6971 Test Method for Measurement of Hindered Phenolic and Aromatic Amine Antioxidant Content in Non-zinc Turbine Oils by Linear Sweep Voltammetry
D7042 Test Method for Dynamic Viscosity and Density of Liquids by Stabinger Viscometer (and the Calculation of Kinematic Viscosity)
D7596 Test Method for Automatic Particle Counting and Particle Shape Classification of Oils Using a Direct Imaging Integrated Tester
D7669 Guide for Practical Lubricant Condition Data Trend Analysis
D7690 Practice for Microscopic Characterization of Particles from In-Service Lubricants by Analytical Ferrography
D7720 Guide for Statistically Evaluating Measurand Alarm Limits when Using Oil Analysis to Monitor Equipment and Oil for Fitness and Contamination
D7843 Test Method for Measurement of Lubricant Generated Insoluble Color Bodies in In-Service Turbine Oils using Membrane Patch Colorimetry
D8112 Guide for Obtaining In-Service Samples of Turbine Operation Related Lubricating Fluid
E659 Test Method for Autoignition Temperature of Chemicals
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D8323-20, Standard Guide for Management of In-Service Phosphate Ester-based Fluids for Steam Turbine Electro-Hydraulic Control (EHC) Systems, ASTM International, West Conshohocken, PA, 2020, www.astm.orgBack to Top