| ||Format||Pages||Price|| |
|5||$52.00||  ADD TO CART|
|Hardcopy (shipping and handling)||5||$52.00||  ADD TO CART|
|Standard + Redline PDF Bundle||10||$62.00||  ADD TO CART|
Significance and Use
5.1 Hydrogen is delivered to fuel cell powered automotive vehicles and stationary appliances at pressures up to 87.5 MPa. The quality of hydrogen delivered is a significant factor in maximizing fuel cell efficiency and life span. Contamination can occur during the production of fuel cell feed gases, contaminating storage containers, station tubing, and fuel lines used for fuel delivery. Collection of a representative fuel sample without the introduction of contaminants even as low as parts-per-billion (ppb) per contaminant during collection is crucial for assessing the quality of fuel in real world applications.
5.2 This practice is intended for application to high pressure, high purity hydrogen; however, the apparatus design and sampling techniques may be applicable to collection of other fuel cell feed gases. Many of the techniques used in this practice can be applied to lower pressure/lower purity gas streams.
1.1 This standard practice describes a sampling procedure of high pressure hydrogen at fueling stations operating at 35 or 70 megapascals (MPa) using a hydrogen quality sampling apparatus (HQSA).
1.2 This practice does not include the analysis of the acquired sample. Applicable ASTM standards include but are not limited to test methods referenced in Section of this practice.
1.3 This practice is not intended for sampling and measuring particulate matter in high pressure hydrogen. For procedures on sampling and measuring particulate matter see ASTM and .
1.4 The values stated in SI units are standard. The values stated in inch-pounds are for information only.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.
1.6 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D4150 Terminology Relating to Gaseous Fuels
D7650 Test Method for Sampling of Particulate Matter in High Pressure Hydrogen used as a Gaseous Fuel with an In-Stream Filter
D7651 Test Method for Gravimetric Measurement of Particulate Concentration of Hydrogen Fuel
ICS Number Code 27.075 (Hydrogen technologies)
UNSPSC Code 15111500(Gaseous fuels)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D7606-17, Standard Practice for Sampling of High Pressure Hydrogen and Related Fuel Cell Feed Gases, ASTM International, West Conshohocken, PA, 2017, www.astm.orgBack to Top