| ||Format||Pages||Price|| |
|20||$54.00||  ADD TO CART|
|Hardcopy (shipping and handling)||20||$54.00||  ADD TO CART|
Significance and Use
4.1 The integrity test methods described are used to determine the integrity of membrane systems, and are applicable to systems containing membrane module configurations of both hollow fiber and flat sheet; such as, spiral-wound configuration. In all cases the practices apply to membranes in the RO, NF, and UF membrane classes. However, the TOC and Dye Test practices do not apply to membranes in the MF range or the upper end of the UF pore size range (0.01 μm and larger pore sizes) due to insignificant or inconsistent removal of TOC material by these membranes.
4.2 These methods may be used to identify relative changes in the integrity of a system, or used in conjunction with the equations described in , to provide a means of estimating the integrity in terms of log reduction value. For critical applications, estimated log reductions using these equations should be confirmed by experiment for the particular membrane and system configuration used.
4.3 The ability of the methods to detect any given defect is affected by the size of the system or portion of the system tested. Selecting smaller portions of the system to test will increase the sensitivity of the test to defects. When determining the size that can be tested as a discrete unit, use the guidelines supplied by the system manufacturer or the general guidelines provided in this practice.
4.4 The applicability of the tests is largely independent of system size when measured in terms of the impact of defects on the treated water quality (that is, the system LRV). This is because the bypass flow from any given defect is diluted in proportion to the systems total flowrate. For example, a 10-module system with a single defect will produce the same water quality as a 100-module system with ten of the same size defects.
1.1 This practice covers the determination of the integrity of water filtration membrane elements and systems using air based tests (pressure decay and vacuum hold), soluble dye, continuous monitoring particulate light scatter techniques, and TOC monitoring tests for the purpose of rejecting particles and microbes. The tests are applicable to systems with membranes that have a nominal pore size less than about 1 µm. The TOC, and Dye, tests are generally applicable to NF and RO class membranes only.
1.2 This practice does not purport to cover all available methods of integrity testing.
1.3 The values stated in SI units are to be regarded as standard. No other units of measurement are included in this standard.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.
1.5 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1129 Terminology Relating to Water
D2777 Practice for Determination of Precision and Bias of Applicable Test Methods of Committee D19 on Water
D3370 Practices for Sampling Water from Closed Conduits
D3864 Guide for On-Line Monitoring Systems for Water Analysis
D3923 Practices for Detecting Leaks in Reverse Osmosis and Nanofiltration Devices
D4839 Test Method for Total Carbon and Organic Carbon in Water by Ultraviolet, or Persulfate Oxidation, or Both, and Infrared Detection
D5173 Guide for On-Line Monitoring of Total Organic Carbon in Water by Oxidation and Detection of Resulting Carbon Dioxide
D5904 Test Method for Total Carbon, Inorganic Carbon, and Organic Carbon in Water by Ultraviolet, Persulfate Oxidation, and Membrane Conductivity Detection
D5997 Test Method for On-Line Monitoring of Total Carbon, Inorganic Carbon in Water by Ultraviolet, Persulfate Oxidation, and Membrane Conductivity Detection
D6161 Terminology Used for Microfiltration, Ultrafiltration, Nanofiltration and Reverse Osmosis Membrane Processes
D6698 Test Method for On-Line Measurement of Turbidity Below 5 NTU in Water
E20 Practice for Particle Size Analysis of Particulate Substances in the Range of 0.2 to 75 Micrometres by Optical Microscopy
E128 Test Method for Maximum Pore Diameter and Permeability of Rigid Porous Filters for Laboratory Use
F658 Practice for Calibration of a Liquid-Borne Particle Counter Using an Optical System Based Upon Light Extinction
ICS Number Code 13.060.01 (Water quality in general)
UNSPSC Code 47101500(Water treatment and supply equipment)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D6908-06(2017), Standard Practice for Integrity Testing of Water Filtration Membrane Systems, ASTM International, West Conshohocken, PA, 2017, www.astm.orgBack to Top