| ||Format||Pages||Price|| |
|6||$45.00||  ADD TO CART|
|Hardcopy (shipping and handling)||6||$45.00||  ADD TO CART|
Significance and Use
The CEDI devices can be used to produce deionized water from feeds of pretreated water. This test method permits the relatively rapid measurement of key performance capabilities of CEDI devices using standard sets of conditions. The data obtained can be analyzed to provide information on whether changes may have occurred in operating characteristics of the device independently of any variability in feed water characteristics or operating conditions. Under specific circumstances, this test method may also provide sufficient information for plant design.
1.1 This test method covers the determination of the operating characteristics of continuous electrodeionization (CEDI) devices using synthetic feed solutions and is not necessarily applicable to natural waters. This test method is a procedure applicable to solutions with a conductivity range from approximately 50 to 1000 μS/cm.
1.2 This test method covers the determination of operating characteristics under standard test conditions of CEDI devices where the electrically active transfer media therein is predominantly unregenerated. This results in more rapid achievement of steady state and shorter test time than when performing a test which requires the active media be predominantly regenerated.
1.3 This test method is not necessarily indicative of the following:
1.3.1 Long-term performance on feed waters containing foulants or sparingly soluble solutes, or both,
1.3.2 Performance on feeds of brackish water, sea water, or other high-salinity feeds,
1.3.3 Performance on synthetic industrial feed solutions, pharmaceuticals, or process solutions of foods and beverages, or,
1.3.4 Performance on feed waters less than 50 μS/cm, particularly performance relating to organic solutes, colloidal or particulate matter, or biological or microbial matter.
1.4 This test method, subject to the limitations previously described, can be applied as either an aid to predict expected deionization performance for a given feed water quality, or as a test method to determine whether performance of a given device has changed over some period of time. It is ultimately, however, the user's responsibility to ensure the validity of this test method for their specific applications.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability or regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1125 Test Methods for Electrical Conductivity and Resistivity of Water
D1129 Terminology Relating to Water
D1193 Specification for Reagent Water
D1293 Test Methods for pH of Water
D2777 Practice for Determination of Precision and Bias of Applicable Test Methods of Committee D19 on Water
D4189 Test Method for Silt Density Index (SDI) of Water
ICS Number Code 25.220.20 (Surface treatment)
UNSPSC Code 41104202(Deionization or demineralization equipment)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D6529-11, Standard Test Method for Operating Performance of Continuous Electrodeionization Systems on Feeds from 50–1000 μS/cm, ASTM International, West Conshohocken, PA, 2011, www.astm.orgBack to Top