| ||Format||Pages||Price|| |
|4||$40.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$40.00||  ADD TO CART|
This specification covers cured-in-place thermosetting resin pipe (CIPP) with a certain measurement, equivalent diameter, for use in gravity flow systems in conveying sanitary sewage, storm water, and certain industrial wastes. This specification is suited for the evaluation and testing of materials used in the rehabilitation of existing pipes by the installation and cure of a resin-impregnated fabric liner. CIPP are classified into three types: Type I which is designed to provide chemical resistance and prevent exfiltration; Type II which is installed in a partially deteriorated existing pipe or structure and is designed to provide chemical resistance, prevent exfiltration and infiltration, and support the external hydrostatic loads due to groundwater only (and internal vacuum, where applicable), since the soil and live loads can be supported by the original conduit or structure; and Type III which is Installed in a fully deteriorated existing pipe or structure and designed to provide chemical resistance, prevent exfiltration and infiltration, and support all external hydraulic, soil, and live loads acting on the original conduit or structure. CIPP also are classified into three grades: Grade 1 as thermosetting polyester resin, Grade 2 as thermosetting polyester resin, and Grade 3 as thermosetting epoxy resin. Properties of CIPP materials such as diameter, wall thickness, chemical resistance, flexural strength, and tensile strength shall be determined by subjecting them to different tests.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers cured-in-place thermosetting resin pipe (CIPP), 4 through 132-in. (100 through 3353-mm) equivalent diameter, for use in gravity flow systems for conveying sanitary sewage, storm water, and certain industrial wastes. This specification is suited for the evaluation and testing of materials used in the rehabilitation of existing pipes by the installation and cure of a resin-impregnated fabric liner.
1.2 This specification can also be extended to cover manholes, pump stations, wetwells, vaults, storage tanks, and other similar structures where a cured in place liner using thermosetting resin is applicable.
1.3 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.4 The following safety hazards caveat pertains only to the test methods portion, Section 8, of this specification: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D543 Practices for Evaluating the Resistance of Plastics to Chemical Reagents
D638 Test Method for Tensile Properties of Plastics
D695 Test Method for Compressive Properties of Rigid Plastics
D790 Test Methods for Flexural Properties of Unreinforced and Reinforced Plastics and Electrical Insulating Materials
D883 Terminology Relating to Plastics
D1600 Terminology for Abbreviated Terms Relating to Plastics
D3039/D3039M Test Method for Tensile Properties of Polymer Matrix Composite Materials
D3567 Practice for Determining Dimensions of Fiberglass (Glass-Fiber-Reinforced Thermosetting Resin) Pipe and Fittings
D3681 Test Method for Chemical Resistance of Fiberglass (Glass-Fiber-Reinforced Thermosetting-Resin) Pipe in a Deflected Condition
D4814 Specification for Automotive Spark-Ignition Engine Fuel
F412 Terminology Relating to Plastic Piping Systems
F1216 Practice for Rehabilitation of Existing Pipelines and Conduits by the Inversion and Curing of a Resin-Impregnated Tube
F1743 Practice for Rehabilitation of Existing Pipelines and Conduits by Pulled-in-Place Installation of Cured-in-Place Thermosetting Resin Pipe (CIPP)
F2019 Practice for Rehabilitation of Existing Pipelines and Conduits by the Pulled in Place Installation of Glass Reinforced Plastic (GRP) Cured-in-Place Thermosetting Resin Pipe (CIPP)
ICS Number Code 23.040.20 (Plastic pipes)
UNSPSC Code 13101900(Thermoset plastics)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D5813-04(2012), Standard Specification for Cured-In-Place Thermosetting Resin Sewer Piping Systems, ASTM International, West Conshohocken, PA, 2012, www.astm.orgBack to Top