| ||Format||Pages||Price|| |
|5||$52.00||  ADD TO CART|
|Hardcopy (shipping and handling)||5||$52.00||  ADD TO CART|
|Standard + Redline PDF Bundle||10||$62.00||  ADD TO CART|
Significance and Use
4.1 Establishment of an in-service coatings monitoring program permits planning and prioritization of coatings maintenance work as needed to maintain coating integrity and performance in nuclear CSL I coating systems. For additional information on nuclear maintenance coating work, refer to ASTM MNL8.
4.2 A coatings monitoring program enables early identification and detection of potential problems in coating systems. Some CSL I coating systems may be known in advance to be suspect, deficient, or unqualified. Monitoring coating performance will assist in developing follow-up procedures to resolve any significant deficiency relative to coating work.
4.3 Degraded coatings may generate debris under design basis accident conditions that could adversely affect the performance of the post-accident safety systems. A coatings monitoring program may be required to fulfill safety analysis report and generic letter commitments for CSL I coating work in a nuclear power plant facility.
1.1 This standard covers procedures for establishing a monitoring program for condition assessment of Coating Service Level (CSL) I coating systems in operating nuclear power plants. Monitoring is an ongoing process of evaluating the condition and performance of the in-service coating systems.
1.2 It is the intent of this standard to provide a recommended basis for establishing a coatings condition assessment program, not to mandate a singular basis for all programs. Variations or simplifications of the program described in this standard may be appropriate for each operating nuclear power plant depending on their licensing commitments.
1.3 This requirements of ASME Section XI, In-Service Inspection Subsections IWE and IWL are beyond the scope of this standard.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D610 Practice for Evaluating Degree of Rusting on Painted Steel Surfaces
D714 Test Method for Evaluating Degree of Blistering of Paints
D3359 Test Methods for Measuring Adhesion by Tape Test
D4538 Terminology Relating to Protective Coating and Lining Work for Power Generation Facilities
D4541 Test Method for Pull-Off Strength of Coatings Using Portable Adhesion Testers
D5498 Guide for Developing a Training Program for Personnel Performing Coating and Lining Work Inspection for Nuclear Facilities
D6677 Test Method for Evaluating Adhesion by Knife
D7091 Practice for Nondestructive Measurement of Dry Film Thickness of Nonmagnetic Coatings Applied to Ferrous Metals and Nonmagnetic, Nonconductive Coatings Applied to Non-Ferrous Metals
D7108 Guide for Establishing Qualifications for a Nuclear Coatings Specialist
D7234 Test Method for Pull-Off Adhesion Strength of Coatings on Concrete Using Portable Pull-Off Adhesion Testers
ICS Number Code 27.120.20 (Nuclear power plants. Safety)
UNSPSC Code 31211504(Coating paints)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D5163-16, Standard Guide for Establishing a Program for Condition Assessment of Coating Service Level I Coating Systems in Nuclear Power Plants, ASTM International, West Conshohocken, PA, 2016, www.astm.orgBack to Top