| ||Format||Pages||Price|| |
|7||$50.00||  ADD TO CART|
|Hardcopy (shipping and handling)||7||$50.00||  ADD TO CART|
|Standard + Redline PDF Bundle||14||$60.00||  ADD TO CART|
Significance and Use
4.1 Sodium is a pervasive contaminant and it is the first cation to break through deionization equipment. This test method allows measuring sodium in low-sodium waters at micrograms per litre (parts per billion) concentrations to identify contamination or to monitor equipment performance. Applications include monitoring makeup systems, condensers, condensate polishers, feedwater, boilerwater, and steam.
4.2 This test method is more sensitive and selective than conductivity measurements on high purity samples.
1.1 This test method covers the on-line determination of trace amounts of sodium in water using an ion-selective electrode.
1.2 This test method is based on on-line application of the sodium ion electrode as reported in the technical literature (. ) It is generally applicable over the range of 0.01 to 10 000 μg/L.
1.3 The analyst should be aware that adequate collaborative data for precision and bias statements as required by Practice are not provided. See Section for details.
1.4 The values stated in SI units are to be regarded as standard. The values given in parentheses after SI units are provided for information only and are not considered standard.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use. For specific hazard statements see Section .
1.6 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1066 Practice for Sampling Steam
D1129 Terminology Relating to Water
D1193 Specification for Reagent Water
D1293 Test Methods for pH of Water
D2777 Practice for Determination of Precision and Bias of Applicable Test Methods of Committee D19 on Water
D3370 Practices for Sampling Water from Flowing Process Streams
D3864 Guide for On-Line Monitoring Systems for Water Analysis
D5540 Practice for Flow Control and Temperature Control for On-Line Water Sampling and Analysis
ICS Number Code 13.060.50 (Examination of water for chemical substances)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D2791-19, Standard Test Method for On-Line Determination of Sodium in Water, ASTM International, West Conshohocken, PA, 2019, www.astm.orgBack to Top