| ||Format||Pages||Price|| |
|4||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$44.00||  ADD TO CART|
|Standard + Redline PDF Bundle||8||$52.00||  ADD TO CART|
This specification covers resilient connectors between reinforced concrete manhole structures, pipes, and laterals. Resilient materials for connectors and filler rings shall be manufactured from natural or synthetic rubber and shall conform to the prescribed requirements. Mechanical devices shall be made from a material or materials in combination that will ensure durability, strength, resistance to corrosion, and have properties that will ensure continued resistance to leakage. The design of pipe connectors and pipe stubs are specified. The physical properties and chemical composition shall conform to the required tests for chemical resistance, tensile strength, elongation at break, hardness, accelerated oven-aging, compression set, water absorption, ozone resistance, low-temperature brittle point, and tear resistance.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers the minimum performance and material requirements for resilient connectors used for connections between reinforced concrete manholes conforming to Specification and pipes, between wastewater structures and pipes, and between precast reinforced concrete pipe and laterals.
1.1.1 These connectors are designed to minimize leakage between the pipe and manhole, and between the pipe and lateral.
1.2 The values stated in inch pound or SI units are to be regarded separately as standard. The SI units are shown in brackets. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in nonconformance with the standard.
Note 1: This specification covers the design, material, and performance of the resilient connection only. Connections covered by this specification are adequate for hydrostatic pressures up to 13 psi (30 ft) [90 kPa (9.1 m)] without leakage when tested in accordance with Section . Infiltration or exfiltration quantities for an installed system are dependent upon many factors other than the connections between manhole structures and pipe, and allowable quantities must be covered by other specifications and suitable testing of the installed pipeline and system.
1.3 The following precautionary caveat pertains only to the test methods portion, Section This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use. , of this specification:For a specific precaution statement, see .
1.4 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
A493 Specification for Stainless Steel Wire and Wire Rods for Cold Heading and Cold Forging
A666 Specification for Annealed or Cold-Worked Austenitic Stainless Steel Sheet, Strip, Plate, and Flat Bar
C478/C478M Specification for Circular Precast Reinforced Concrete Manhole Sections
C822 Terminology Relating to Concrete Pipe and Related Products
C913 Specification for Precast Concrete Water and Wastewater Structures
D395 Test Methods for Rubber PropertyCompression Set
D412 Test Methods for Vulcanized Rubber and Thermoplastic ElastomersTension
D471 Test Method for Rubber PropertyEffect of Liquids
D543 Practices for Evaluating the Resistance of Plastics to Chemical Reagents
D573 Test Method for RubberDeterioration in an Air Oven
D624 Test Method for Tear Strength of Conventional Vulcanized Rubber and Thermoplastic Elastomers
D883 Terminology Relating to Plastics
D1149 Test Methods for Rubber DeteriorationCracking in an Ozone Controlled Environment
D1566 Terminology Relating to Rubber
D2137 Test Methods for Rubber PropertyBrittleness Point of Flexible Polymers and Coated Fabrics
D2240 Test Method for Rubber PropertyDurometer Hardness
ICS Number Code 93.030 (External sewerage systems)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM C923 / C923M-20, Standard Specification for Resilient Connectors Between Reinforced Concrete Manhole Structures, Pipes, and Laterals, ASTM International, West Conshohocken, PA, 2020, www.astm.orgBack to Top