| ||Format||Pages||Price|| |
|4||$46.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$46.00||  ADD TO CART|
|Standard + Redline PDF Bundle||8||$54.00||  ADD TO CART|
This specification covers extra strength and standard strength vitrified clay pipe and fittings to be used for the conveyance of sewage, industrial wastes, and storm water; and extra strength perforated and standard strength perforated vitrified clay pipe to be used for underdrainage, filter fields, leaching fields, and similar subdrainage installations. Vitrified clay pipe shall be manufactured from fire clay, shale, surface clay, or a combination of these materials that, when formed into pipe and fired to suitable temperatures. Pipe shall meet the bearing strength requirements prescribed. The manufacturer shall at his option, apply either a hydrostatic pressure test or an absorption test to all of the test specimens in each size and run of the pipe. The absorption of vitrified clay pipe shall not exceed 8%. The acid resistance test is used to determine the resistance of pipe to the action of acids encountered in sanitary sewers.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification establishes the criteria for acceptance, prior to installation, of extra strength and standard strength vitrified clay pipe and fittings to be used for the conveyance of sewage, industrial wastes, and storm water; and extra strength perforated and standard strength perforated vitrified clay pipe to be used for underdrainage, filter fields, leaching fields, and similar subdrainage installations.
1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
Note 1: Attention is called to Specification , Test Method , Test Method , Test Methods , and Terminology .
1.3 The following precautionary caveat pertains only to the Test Method portion, This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use. of this standard:
1.4 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C301 Test Methods for Vitrified Clay Pipe
C425 Specification for Compression Joints for Vitrified Clay Pipe and Fittings
C828 Test Method for Low-Pressure Air Test of Vitrified Clay Pipe Lines
C896 Terminology Relating to Clay Products
C1091 Test Method for Hydrostatic Infiltration Testing of Vitrified Clay Pipe Lines
ICS Number Code 23.040.50 (Pipes and fittings of other materials)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM C700-18, Standard Specification for Vitrified Clay Pipe, Extra Strength, Standard Strength, and Perforated, ASTM International, West Conshohocken, PA, 2018, www.astm.orgBack to Top