| ||Format||Pages||Price|| |
|4||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$44.00||  ADD TO CART|
|Standard + Redline PDF Bundle||8||$52.00||  ADD TO CART|
Significance and Use
5.1 This is not a routine test. The values recorded are applicable only to the sewer being tested and at the time of testing.
1.1 This test method covers procedures for testing concrete pipe sewerlines, when using the negative air pressure (vacuum) test method to demonstrate the integrity of the installed material and the construction procedures. This test method covers testing of 100 to 900-mm diameter circular concrete pipe sewerlines utilizing gasketed joints.
Note 1: The user of this specification is advised that methods described in this test method may also be used as a preliminary test to enable the manufacturer or installer to demonstrate the condition of sewer pipe prior to delivery or backfill. Minimum test times presented in
Note 2: The user of this test method is advised that the negative air pressure (vacuum) test criteria presented in this test method are similar to those in general use. The test and criteria have been used widely and successfully in testing smaller diameter pipe. Larger pipe will be accepted more conveniently by visual inspection and individual joint testing.
Note 3: Test times tabulated and the rate of air loss in this standard are based on successful testing of installed pipelines. However, since air and water have different physical properties, retests of some pipelines not meeting field air tests have been successful when tested with water.
1.2 This test method is the SI companion to Test Method .
1.3 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use. See Section for specific safety precautions.
1.4 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C822 Terminology Relating to Concrete Pipe and Related Products
C969 Practice for Infiltration and Exfiltration Acceptance Testing of Installed Precast Concrete Pipe Sewer Lines
ICS Number Code 23.040.50 (Pipes and fittings of other materials)
UNSPSC Code 40171510(Commercial concrete pipe)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM C1214M-19, Standard Test Method for Concrete Pipe Sewerlines by Negative Air Pressure (Vacuum) Test Method (Metric), ASTM International, West Conshohocken, PA, 2019, www.astm.orgBack to Top