| ||Format||Pages||Price|| |
|8||$54.00||  ADD TO CART|
|Hardcopy (shipping and handling)||8||$54.00||  ADD TO CART|
|Standard + Redline PDF Bundle||16||$64.00||  ADD TO CART|
This guide establishes requirements for seamless and welded copper-nickel tubes for use in heat exchangers in water desalting plants. Seamless tubes shall be manufactured by hot extrusion or piercing, and subsequent cold working and annealing as to produce a uniform, seamless wrought structure in the finished product. The welded tubes shall be manufactured from flat rolled strip which is subsequently formed and welded by a forge-weld process or a fusion-weld process. For forged-welded tube, the edges of the strip shall be heated to a required welding temperature, usually by high-frequency electric current, and be pressed firmly together causing a forged-type joint to be formed with internal and external flash or bead. On the other hand, fusion-welded tube shall be mechanically worked to produce a smooth external and internal surface without the application of scarfing or other removal of the weld bead. The product shall be cold worked and annealed as necessary to meet properties of the temper specified. The test specimen shall be free of defects, but blemishes of a nature that do not interfere with the intended application are acceptable for the following tests: expansion test, flattening test, and reverse-bend test. Forged-welded and annealed tubes shall have a completely recrystallized grain structure, and the weld zone shall have a structure typical of hot-forged welds. Fusion-welded and annealed tube shall have a structure typical of a fusion weld on its weld zone. The product shall be clean and free from defects, but blemishes of a nature that do not interfere with the intended application are acceptable.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification establishes requirements for seamless and welded copper-nickel tubes from 0.250 to 2.125 in. (6.35 to 54.0 mm) in diameter for use in heat exchangers in water desalting plants. The following alloys are involved:
Type of Metal
1.2 Units—Values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.3 The following safety hazard caveat pertains only to the test methods of Section described in this specification: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to its use.
1.4 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
B153 Test Method for Expansion (Pin Test) of Copper and Copper-Alloy Pipe and Tubing
B154 Test Method for Mercurous Nitrate Test for Copper Alloys
B601 Classification for Temper Designations for Copper and Copper AlloysWrought and Cast
B846 Terminology for Copper and Copper Alloys
B858 Test Method for Ammonia Vapor Test for Determining Susceptibility to Stress Corrosion Cracking in Copper Alloys
B968/B968M Test Method for Flattening of Copper and Copper-Alloy Pipe and Tube
E3 Guide for Preparation of Metallographic Specimens
E8/E8M Test Methods for Tension Testing of Metallic Materials
E62 Test Methods for Chemical Analysis of Copper and Copper Alloys (Photometric Methods)
E76 Test Methods for Chemical Analysis of Nickel-Copper Alloys
E118 Test Methods for Chemical Analysis of Copper-Chromium Alloys
E243 Practice for Electromagnetic (Eddy Current) Examination of Copper and Copper-Alloy Tubes
E255 Practice for Sampling Copper and Copper Alloys for the Determination of Chemical Composition
E478 Test Methods for Chemical Analysis of Copper Alloys
ICS Number Code 77.150.30 (Copper products)
UNSPSC Code 40101802(Heat exchangers); 40182000(Seamless copper tubes)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM B552-19, Standard Specification for Seamless and Welded Copper–Nickel Tubes for Water Desalting Plants, ASTM International, West Conshohocken, PA, 2019, www.astm.orgBack to Top