| ||Format||Pages||Price|| |
|9||$52.00||  ADD TO CART|
|Hardcopy (shipping and handling)||9||$52.00||  ADD TO CART|
|Standard + Redline PDF Bundle||18||$62.00||  ADD TO CART|
This specification covers the requirements for seamless UNS C10200, C12000, or C12200 copper alloy tubes used for connection, repairs, or alternations of field air conditioning or refrigeration units. Materials in the form of billets, bars, or tubes should be used to produce a homogeneous uniform wrought structure by either hot or cold working. Each tube should be cold drawn to the finished size and wall thickness. Coiled lengths with soft annealed tempers should be bright annealed after coiling then dehydrated and either capped, plugged, crimped, or otherwise closed at both ends. Straight lengths with hard drawn tempers should be cleaned and either capped, plugged, or otherwise closed at both ends. The grain sizes, tensile properties, and eddy-current and cleanness test results should conform to the values listed herein.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification establishes the requirements for seamless copper tube intended for use in the connection, repairs, or alternations of air conditioning or refrigeration units in the field.
Note 1: Fittings used for soldered or brazed connections in air conditioning and refrigeration systems are described in ASME Standard B16.22.
Note 2: The assembly of copper tubular systems by soldering is described in Practice .
Note 3: Solders for joining copper tubular systems are described in Specification . The requirements for acceptable fluxes for these systems are described in Specification .
1.2 The tube shall be produced from the following coppers, and the manufacturer has the option to supply any one of them, unless otherwise specified:
Oxygen free without
1.3 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.4 The following hazard statement pertains only to the test method described in of this specification: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.
1.5 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
B32 Specification for Solder Metal
B153 Test Method for Expansion (Pin Test) of Copper and Copper-Alloy Pipe and Tubing
B577 Test Methods for Detection of Cuprous Oxide (Hydrogen Embrittlement Susceptibility) in Copper
B601 Classification for Temper Designations for Copper and Copper AlloysWrought and Cast
B813 Specification for Liquid and Paste Fluxes for Soldering of Copper and Copper Alloy Tube
B828 Practice for Making Capillary Joints by Soldering of Copper and Copper Alloy Tube and Fittings
B900 Practice for Packaging of Copper and Copper Alloy Mill Products for U.S. Government Agencies
E3 Guide for Preparation of Metallographic Specimens
E8/E8M Test Methods for Tension Testing of Metallic Materials
E29 Practice for Using Significant Digits in Test Data to Determine Conformance with Specifications
E53 Test Method for Determination of Copper in Unalloyed Copper by Gravimetry
E62 Test Methods for Chemical Analysis of Copper and Copper Alloys (Photometric Methods)
E112 Test Methods for Determining Average Grain Size
E243 Practice for Electromagnetic (Eddy Current) Examination of Copper and Copper-Alloy Tubes
E255 Practice for Sampling Copper and Copper Alloys for the Determination of Chemical Composition
ICS Number Code 23.040.15 (Non-ferrous metal pipes)
UNSPSC Code 40182000(Seamless copper tubes); 73161517(Air conditioning or ventilating or refrigeration equipment manufacture services)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM B280-20, Standard Specification for Seamless Copper Tube for Air Conditioning and Refrigeration Field Service, ASTM International, West Conshohocken, PA, 2020, www.astm.orgBack to Top