| ||Format||Pages||Price|| |
|7||$46.00||  ADD TO CART|
|Hardcopy (shipping and handling)||7||$46.00||  ADD TO CART|
|Standard + Redline PDF Bundle||14||$55.20||  ADD TO CART|
This specification covers black and hot-dipped zinc-coated (galvanized) welded and seamless steel pipe for fire protection use. The pipe may be bent, but it is not intended for bending made at ambient temperature wherein the inside diameter of the bend is less than twelve times the outside diameter of the pipe being bent. The steel shall conform to the required chemical composition. Each length of pipe shall be subjected to a hydrostatic test without leakage through the pipe wall. As an alternative to the hydrostatic test, and when accepted by the purchaser, each pipe shall be tested with a non-destructive electrical method. Finally, flattening test shall be performed on the pipe in accordance with, electric-resistance-welded pipe, and furnace-welded pipe.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers black and hot-dipped galvanized welded and seamless steel pipe in NPS 1/2 to NPS 10, inclusive [DN 15 to DN 250, inclusive] (Note 1), with wall thicknesses as given in Table 1 and Table 2. Pipe having other wall thicknesses may be furnished provided such pipe complies with all other requirements of this specification and the outside diameter is as given in Table 2. Pipe ordered under this specification is intended for use in fire protection systems. The pipe may be bent, but it is not intended for bending made at ambient temperature wherein the inside diameter of the bend is less than twelve times the outside diameter of the pipe being bent (Note 2).
1.2.1 Light-Weight Fire Protection Pipe—Rolled groove, welding, and fittings for plain end pipe. See Table 1 for dimensions.
1.2.2 Standard-Weight Fire Protection Pipe—Cut or rolled groove, threading, welding, and fittings for plain end pipe. See Table 2 for dimensions.
1.3 The following safety hazards caveat pertains only to the test method portion, Sections 8, 9, and 10, of this specification: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
1.4 The values stated in either SI units or inch-pound units are to be regarded separately as standard. Within the text, the SI units are shown in brackets. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in non-conformance with the standard.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
ASME StandardsB1.20.1 Pipe Threads, General Purpose, Inch Available from American Society of Mechanical Engineers (ASME), ASME International Headquarters, Three Park Ave., New York, NY 10016-5990, http://www.asme.org. B36.10 Welded and Seamless Wrought Steel Pipe B36.19 Stainless Steel Pipe
Federal StandardFed. Std. No. 123 Marking for Shipments (Civil Agencies) Available from Standardization Documents Order Desk, Bldg. 4 Section D, 700 Robbins Ave., Philadelphia, PA 19111-5094, Attn: NPODS.
Military StandardsMIL-STD-129 Marking for Shipment and Storage MIL-STD-163 Steel Mill Products, Preparation for Shipment and Storage
A90/A90M Test Method for Weight [Mass] of Coating on Iron and Steel Articles with Zinc or Zinc-Alloy Coatings
A700 Practices for Packaging, Marking, and Loading Methods for Steel Products for Shipment
A751 Test Methods, Practices, and Terminology for Chemical Analysis of Steel Products
A865 Specification for Threaded Couplings, Steel, Black or Zinc-Coated (Galvanized) Welded or Seamless, for Use in Steel Pipe Joints
B6 Specification for Zinc
E213 Practice for Ultrasonic Testing of Metal Pipe and Tubing
E309 Practice for Eddy-Current Examination of Steel Tubular Products Using Magnetic Saturation
E570 Practice for Flux Leakage Examination of Ferromagnetic Steel Tubular Products
ICS Number Code 23.040.10 (Iron and steel pipes)
UNSPSC Code 40171601(Industrial welded carbon steel pipe); 40171602(Industrial seamless carbon steel pipe)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM A795 / A795M-13, Standard Specification for Black and Hot-Dipped Zinc-Coated (Galvanized) Welded and Seamless Steel Pipe for Fire Protection Use, ASTM International, West Conshohocken, PA, 2013, www.astm.orgBack to Top