| ||Format||Pages||Price|| |
|PDF (164K)||11||$25||  ADD TO CART|
|Complete Source PDF (3.7M)||286||$55||  ADD TO CART|
Every commercial nuclear power reactor pressure vessel (RPV) is required to have a reactor vessel surveillance program at the time of plant licensing. The program is part of a continuing structural integrity assessment of the RPV. As such, the surveillance program supplements Section III of the American Society of Mechanical Engineers (ASME) Code ,1 which is the design basis for nuclear power plant component pressure boundaries. The Code assumes that the materials of construction are ductile in the evaluation and design of all components. The surveillance program for each RPV is intended to provide assurance of continued applicability of the ASME Code, Appendix G, assessment of that RPV's operating limits. This assessment ensures that the RPV is always in a condition which precludes the unstable propagation of flaws in the vessel wall material.