| ||Format||Pages||Price|| |
|31||$89.00||  ADD TO CART|
1.1 This specification covers seamless and welded black and hot-dipped galvanized steel pipe in NPS 1/8 to NPS 26 [DN 6 to DN 650] ( ), inclusive, with nominal wall thickness ( ) as given in and . It shall be permissible to furnish pipe having other dimensions provided that such pipe complies with all other requirements of this specification. Supplementary requirements of an optional nature are provided and shall apply only when specified by the purchaser.
Note 1: The dimensionless designators NPS (nominal pipe size) [DN (diameter nominal)] have been substituted in this specification for such traditional terms as “nominal diameter,” “size,” and “nominal size.”
Note 2: The term nominal wall thickness has been assigned for the purpose of convenient designation, existing in name only, and is used to distinguish it from the actual wall thickness, which may vary over or under the nominal wall thickness.
1.2 This specification covers the following types and grades:
1.2.1 Type F—Furnace-butt-welded, continuous welded Grade A,
1.2.2 Type E—Electric-resistance-welded, Grades A and B, and
1.2.3 Type S—Seamless, Grades A and B.
Note 3: See for definitions of types of pipe.
1.3 Pipe ordered under this specification is intended for mechanical and pressure applications and is also acceptable for ordinary uses in steam, water, gas, and air lines. It is suitable for welding, and suitable for forming operations involving coiling, bending, and flanging, subject to the following qualifications:
1.3.1 Type F is not intended for flanging.
1.3.2 If Type S or Type E is required for close coiling or cold bending, Grade A is the preferred grade; however, this is not intended to prohibit the cold bending of Grade B pipe.
1.3.3 Type E is furnished either nonexpanded or cold expanded at the option of the manufacturer.
1.4 The values stated in either SI units or inch-pound units are to be regarded separately as standard. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in non-conformance with the standard.
1.5 The following precautionary caveat pertains only to the test method portion, Sections This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory requirements prior to use. , , , , , and of this specification:
1.6 The text of this specification contains notes or footnotes, or both, that provide explanatory material. Such notes and footnotes, excluding those in tables and figures, do not contain any mandatory requirements.
1.7 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
2. Documentos Citados
A370 Test Methods and Definitions for Mechanical Testing of Steel Products
A530/A530M Specification for General Requirements for Specialized Carbon and Alloy Steel Pipe
A700 Guide for Packaging, Marking, and Loading Methods for Steel Products for Shipment
A751 Test Methods and Practices for Chemical Analysis of Steel Products
A865/A865M Specification for Threaded Couplings, Steel, Black or Zinc-Coated (Galvanized) Welded or Seamless, for Use in Steel Pipe Joints
A90/A90M Test Method for Weight [Mass] of Coating on Iron and Steel Articles with Zinc or Zinc-Alloy Coatings
B6 Specification for Zinc
E1806 Practice for Sampling Steel and Iron for Determination of Chemical Composition
E213 Practice for Ultrasonic Testing of Metal Pipe and Tubing
E273 Practice for Ultrasonic Testing of the Weld Zone of Welded Pipe and Tubing
E29 Practice for Using Significant Digits in Test Data to Determine Conformance with Specifications
E309 Practice for Eddy Current Examination of Steel Tubular Products Using Magnetic Saturation
E570 Practice for Flux Leakage Examination of Ferromagnetic Steel Tubular Products
MIL-STD-129 Marking for Shipment and Storage Available from Standardization Documents Order Desk, DODSSP, Bldg. 4, Section D, 700 Robbins Ave., Philadelphia, PA 19111-5098
Fed. Std. No. 123 Marking for Shipment (Civil Agencies) Available from General Services Administration, Washington, DC 20405.
Fed. Std. No. 183