SUPERSEDED (click for Active standard)
| ||Format||Pages||Price|| |
|2||$48.00||  ADD TO CART|
1.1 This specification covers minimum-wall-thickness, seamless carbon steel boiler and superheater tubes for high-pressure service.
1.2 The tubing sizes and thicknesses usually furnished to this specification are 1/2 in. to 7 in. [12.7 to 177.8 mm] outside diameter and 0.085 to 1.000 in. [2.2 to 25.4 mm], inclusive, in minimum wall thickness. Tubing having other dimensions may be furnished, provided such tubes comply with all other requirements of this specification.
1.3 Mechanical property requirements do not apply to tubing smaller than 1/8 in. [3.2 mm] inside diameter or 0.015 in. [0.4 mm] thickness.
1.4 When these products are to be used in applications conforming to ISO Recommendations for Boiler Construction, the requirements of Specification A 520 shall supplement and supersede the requirements of this specification.
1.5 The values stated in either inch-pound units or SI units are to be regarded separately as standard. Within the text, the SI units are shown in brackets. The values stated in each system are not exact equivalents; therefore, each system must be used independently of the other. Combining values from the two systems may result in nonconformance with the specification. The inch-pound units shall apply unless the "M" designation of this specification is specified in the order.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
A450/A450M Specification for General Requirements for Carbon and Low Alloy Steel Tubes
ICS Number Code 23.040.10 (Iron and steel pipes)
UNSPSC Code 40182300(Seamless steel tubes)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM A192 / A192M-91(2001), Standard Specification for Seamless Carbon Steel Boiler Tubes for High-Pressure Service, ASTM International, West Conshohocken, PA, 1991, www.astm.orgBack to Top