| ||Format||Pages||Price|| |
|5||$45.00||  ADD TO CART|
|Hardcopy (shipping and handling)||5||$45.00||  ADD TO CART|
Significance and Use
4.1 This practice provides minimum recommendations for the installation of self-leveling underlayments suitable to receive resilient floor coverings. This practice establishes the proper preparation of the subfloor, and installation methods and quality control requirements for self-leveling underlayments. This practice addresses the preparation of the self-leveling underlayment’s surface prior to the installation of floor coverings.
4.2 Actual requirements for self-leveling underlayments are generally included as part of project plans or specifications and may vary from the recommendations set forth in this practice. Provisions in the project documents at variance with this practice shall take precedence.
1.1 This practice covers the installation of self-leveling underlayments, which may include a priming system, over solid wood, wood structural panel subfloors, over concrete, and over certain solidly bonded existing flooring systems such as epoxy floors, ceramic and natural stone tiles, terrazzo, as well as properly prepared non water-soluble adhesive residues as recommended by the underlayment manufacturer. This practice also covers the preparation of the self-leveling underlayment’s surface prior to the installation of resilient flooring.
1.3 This practice does not cover the structural adequacy of the subfloor. The structural integrity of assemblies is governed by local building codes and may be superseded by the resilient flooring manufacturer's requirements.
1.4 This practice does not supersede the self-leveling underlayment manufacturer’s, adhesive manufacturer’s or resilient flooring manufacturer’s written instructions. Consult the individual manufacturer for specific recommendations.
1.5 Many self-leveling underlayments are not suitable for use on concrete slabs on grade or below due to potential moisture problems arising from moisture intrusion. This may occur unless an adequate vapor retarder or vapor barrier is present directly beneath the concrete slab or an effective moisture remediation system has been installed beneath the surface of the self-leveling underlayment. Consult the manufacturer of the self-leveling underlayment and flooring system for specific recommendations.
1.6 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.7 This practice does purport to address the necessity for or the safe or correct removal of asbestos containing materials. Breathing of asbestos dust is hazardous. Asbestos and asbestos products present demonstrated health risks for users and for those with whom they come into contact. In addition to other precautions, when working with asbestos-cement products, minimize the dust that results. For information on the safe use of chrysoltile asbestos, refer to “Safe Use of Chrysotile Asbestos: A Manual on Preventive and Control Measures.”2
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C109/C109M Test Method for Compressive Strength of Hydraulic Cement Mortars (Using 2-in. or [50-mm] Cube Specimens)
C219 Terminology Relating to Hydraulic Cement
C1583 Test Method for Tensile Strength of Concrete Surfaces and the Bond Strength or Tensile Strength of Concrete Repair and Overlay Materials by Direct Tension (Pull-off Method)
C1708 Test Methods for Self-leveling Mortars Containing Hydraulic Cements
F141 Terminology Relating to Resilient Floor Coverings
F710 Practice for Preparing Concrete Floors to Receive Resilient Flooring
F1482 Practice for Installation and Preparation of Panel Type Underlayments to Receive Resilient Flooring
F1869 Test Method for Measuring Moisture Vapor Emission Rate of Concrete Subfloor Using Anhydrous Calcium Chloride
F2170 Test Method for Determining Relative Humidity in Concrete Floor Slabs Using in situ Probes
F2420 Test Method for Determining Relative Humidity on the Surface of Concrete Floor Slabs Using Relative Humidity Probe Measurement and Insulated Hood
ICS Number Code 83.080.10 (Thermosetting materials)
UNSPSC Code 30161700(Flooring)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F2873-13, Standard Practice for the Installation of Self-Leveling Underlayment and the Preparation of Surface to Receive Resilient Flooring, ASTM International, West Conshohocken, PA, 2013, www.astm.orgBack to Top