| ||Format||Pages||Price|| |
|5||$45.00||  ADD TO CART|
|Hardcopy (shipping and handling)||5||$45.00||  ADD TO CART|
Significance and Use
5.1 This practice is for use by specifiers, regulatory agencies, owners and inspection organizations that are involved in the rehabilitation of pressure mains and conduits, and in particular potable water lines in the diameter range of 4 to 12 in. The supplier of the FIPLS lining system product should be consulted for design and installation information.
1.1 This practice covers requirements and test methods for installation of a semi-structural polyethylene (PE) and encapsulated cement mortar formed-in-place lining system (FIPLS) intended for the rehabilitation of water pipelines from 4 in. to 12 in. This renewal process involves installing a folded PE liner with multiple hooks on the outside face into an existing water pipeline then pumping cement mortar into the annular space and progressively reforming the liner against the original pipe wall by means of forcing a reforming device through the pipeline.
1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.3 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Particular attention is drawn to those safety regulations and requirements involving entering into and working in confined spaces.
1.4 This practice is to be used with the material specified in 4.2.1 of the Standard Specification for Polyethylene (PE) and Cement Materials for an Encapsulated Cement Mortar Formed in Place Lining System (FIPLS) for the Rehabilitation of Water Pipelines.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C109/C109M Test Method for Compressive Strength of Hydraulic Cement Mortars (Using 2-in. or [50-mm] Cube Specimens)
D1600 Terminology for Abbreviated Terms Relating to Plastics
F412 Terminology Relating to Plastic Piping Systems
F2718 Specification for Polyethylene (PE) and Cement Materials for an Encapsulated Cement Mortar Formed in Place Liner System (FIPLS) for the Rehabilitation of Water Pipelines
AWWA/ANSI StandardC651 Disinfecting Water Mains Manual M28 Rehabilitation of Water Mains
ICS Number Code 91.100.10 (Cement. Gypsum. Lime. Mortar)
UNSPSC Code 40171500(Commercial pipe and piping)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F2719-09(2015), Standard Practice for Installation of Polyethylene (PE) and Encapsulated Cement Mortar Formed in Place Lining System (FIPLS) for the Rehabilitation of Water Pipelines, ASTM International, West Conshohocken, PA, 2015, www.astm.orgBack to Top