Active Standard ASTM F2551 | Developed by Subcommittee: F36.20
Book of Standards Volume: 04.12
This practice describes the procedures involved in the structural reinforcement, sealing, protection, and rehabilitation of sanitary sewer manholes by the application of a prepackaged protective cementitious liner system to all cleaned interior surface from the bottom of the frame to the bench. The manholes to which the cementitious liner shall be applied may be made of brick, concrete, block, and various other materials. Detailed descriptions are given for all prepackaged materials necessary for this practice that include materials for substrate repairs, cementitious repair materials, infiltration water control materials, cementitious water control materials, chemical grout materials, and lining materials. Detailed descriptions are also provided for each procedure involved here which includes surface preparation, high pressure cleaning, surface repair, mixing of prepackaged cementitious repair materials, spray application of the cement liner by manual surface sealing or centrifugal cast process, and curing of the freshly applied cementitious mortar.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification describes all the work required to structurally reinforce, seal, and protect sanitary sewer manholes. Applications include applying a prepackaged cementitious liner that can function as a full depth restoration or a partial depth repair. A uniform high-strength, fiber-reinforced cementitious mortar should be manually sprayed and hand troweled or centrifugally cast in a uniform, prescribed thickness to all cleaned, interior surfaces from the bottom of the frame to the bench. The cementitious liner may be applied to manholes constructed of brick, concrete, block, and various other materials.
1.2 A manufacturer’s approved applicator shall furnish the complete application of the protective, prepackaged cementitious liner material. All of the cleaning, preparation, and application procedures shall be in accordance with the manufacturer’s recommendations.
1.3 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Manholes are permit required confined spaces in accordance with OSHA definition and should be treated as such, requiring confined space entry permits, appropriate monitoring equipment, and the associated personal protective equipment.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C39/C39M Test Method for Compressive Strength of Cylindrical Concrete Specimens
C109/C109M Test Method for Compressive Strength of Hydraulic Cement Mortars (Using 2-in. or [50-mm] Cube Specimens)
C309 Specification for Liquid Membrane-Forming Compounds for Curing Concrete
C494/C494M Specification for Chemical Admixtures for Concrete
C969 Practice for Infiltration and Exfiltration Acceptance Testing of Installed Precast Concrete Pipe Sewer Lines
C1140 Practice for Preparing and Testing Specimens from Shotcrete Test Panels
C1244 Test Method for Concrete Sewer Manholes by the Negative Air Pressure (Vacuum) Test Prior to Backfill
C1315 Specification for Liquid Membrane-Forming Compounds Having Special Properties for Curing and Sealing Concrete
F2414 Practice for Sealing Sewer Manholes Using Chemical Grouting
ACI StandardsACI 506R Guide to Shotcrete
ICRI Technical GuidelinesGuideline No. 03737 Guide for the Preparation of Concrete Surfaces for Repair Using Hydro-demolition Methods
ICS Number Code 93.030 (External sewerage systems)
UNSPSC Code 47100000(Water and wastewater treatment supply and disposal); 30111500(Concrete and mortars)