WITHDRAWN, NO REPLACEMENT
| ||Format||Pages||Price|| |
|6||$52.80||  ADD TO CART|
This test method covers the quantitative determination of percent relative humidity above the surface of concrete floor slabs for field or laboratory tests.
Formerly under the jurisdiction of Committee F06 on Resilient Floor Coverings, this test method was withdrawn in December 2014. This standard is being withdrawn without replacement because the preliminary Precision and Bias was conducted on December 26, 2013 to March 3, 2014 by ASTM members. When tested over one sealed concrete slab with the surface prepared as described in the latest approved draft of F2420, the results showed that each hood/probe took about 49 days to get within approximately 2 % of its last reading taken after 70 days. That said, at 70 days the six different hood/probe assemblies used had a 9 % difference between them. These results clearly show that even after 70 days they would not be accepted by flooring manufacturers as a go/no-go test method for installing resilient flooring. In addition, even as a test method for investigating installation failures it shows to be inconclusive at 70 days so it has no real value to the industry. The fact that there is an ASTM test method is one reason that other countries use it even though they have never performed any Precision and Bias themselves. Withdrawing this document seems reasonable as there appears to be little value to the industry.
1.1 This test method covers the quantitative determination of percent relative humidity above the surface of concrete floor slabs for field or laboratory tests.
1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.3 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Some specific warnings are given in Section 7.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
E104 Practice for Maintaining Constant Relative Humidity by Means of Aqueous Solutions
F2170 Test Method for Determining Relative Humidity in Concrete Floor Slabs Using in situ Probes
Other StandardsU.S. Department of Housing and Urban Development, Lead-Based Paint: Interim Guidelines for Hazard Identification and Abatement in Public and Indian Housing Available from the U.S. Department of Housing and Urban Development, 451 7th Street SW, Washington, DC 20410.
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F2420-05(2011), Standard Test Method for Determining Relative Humidity on the Surface of Concrete Floor Slabs Using Relative Humidity Probe Measurement and Insulated Hood (Withdrawn 2014), ASTM International, West Conshohocken, PA, 2011, www.astm.orgBack to Top