Active Standard ASTM F2022 | Developed by Subcommittee: F26.06
Book of Standards Volume: 15.12
Historical (view previous versions of standard)
Significance and Use
5.1 The energy input rate test is used to confirm that the booster heater is operating properly prior to further testing.
5.2 Booster heater flow capacity is an indicator of the booster heater's ability to supply hot water for sanitation. The booster heater's flow capacity can be used by the operator to determine the appropriate size booster heater for their operation. Booster heater energy rate is an indicator of the booster heater's energy consumption during continuous water flow. The energy rate can be used by food service operators to estimate the energy consumption of the booster heater. Booster heater energy efficiency is a precise indicator of a booster heater's energy performance during the continuous flow test. This information enables the food service operator to consider energy performance when selecting a booster heater.
5.3 Booster heater flow capacity at 50 % of the maximum capacity is an indicator of the booster heater's ability to provide hot water for sanitation at this reduce flow rate condition. Booster heater energy efficiency at a flow rate of 50 % of maximum capacity is an indicator of a booster heater's energy performance at this flow rate. The booster heater outlet temperature during the capacity test at a flow rate of 50 % of maximum capacity is an indicator of the booster heater's temperature response at this reduced flow rate.
1.1 This test method evaluates the energy efficiency, energy consumption and water heating performance of booster heaters. The food service operator can use this evaluation to select a booster heater and understand its energy consumption.
1.3.1 Energy input rate (9.2).
1.3.2 Pilot energy rate (9.3).
1.3.3 Flow capacity rate, energy rate, and energy efficiency with 110°F (43.3°C) and 140°F (60.0°C) supply to the booster heater inlet (9.4).
1.3.4 Thermostat calibration (9.5).
1.3.5 Energy rate and energy efficiency at 50% of flow capacity rate with 110°F (43.3°C) and 140°F (60.0°C) supply to the booster heater inlet (9.6).
1.3.6 Preheat energy and time (9.7). The preheat test is not applicable to booster heaters built without water storage and will not have auxiliary water storage connected to the booster heater to complete the water heating system.
1.3.7 Idle (standby) energy rate (9.8).
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D3588 Practice for Calculating Heat Value, Compressibility Factor, and Relative Density of Gaseous Fuels
ANSI StandardANSIZ223.1-1996 National Fuel Gas Code
ICS Number Code 91.140.65 (Water heating equipment)