| ||Format||Pages||Price|| |
|9||$45.00||  ADD TO CART|
|Hardcopy (shipping and handling)||9||$45.00||  ADD TO CART|
|Standard + Redline PDF Bundle||18||$54.00||  ADD TO CART|
Significance and Use
This practice is for use by designers and specifiers, regulatory agencies, owners and inspection organizations who are involved in the rehabilitation of conduits through the use of a resin-impregnated fabric tube, pulled in place through an existing conduit and subsequently inflated and cured. As for any standard practice, modifications may be required for specific job conditions.
1.1 This practice covers the procedures for the reconstruction of pipelines and conduits (4 to 60 in. (100 to 1500 mm) diameter) by the pulled-in place installation of a resin-impregnated, flexible fabric tube into an existing conduit followed by inflation with compressed air (see Fig. 1). The resin/fabric tube can be cured by either the flow through the fabric tube of mixed air and steam or hot water or by use of ultraviolet light. When cured, the finished cured-in-place pipe will be continuous and tight fitting. This reconstruction process can be used in a variety of gravity flow applications such as sanitary sewers, storm sewers, process piping, electrical conduits, ventilation systems, and pressure applications.
1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.3 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
FIG. 1 Cured-In-Place Pipe Installation Method (Air/Steam)
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D543 Practices for Evaluating the Resistance of Plastics to Chemical Reagents
D578 Specification for Glass Fiber Strands
D638 Test Method for Tensile Properties of Plastics
D790 Test Methods for Flexural Properties of Unreinforced and Reinforced Plastics and Electrical Insulating Materials
D1600 Terminology for Abbreviated Terms Relating to Plastics
D3039/D3039M Test Method for Tensile Properties of Polymer Matrix Composite Materials
D3567 Practice for Determining Dimensions of Fiberglass (Glass-Fiber-Reinforced Thermosetting Resin) Pipe and Fittings
D5813 Specification for Cured-In-Place Thermosetting Resin Sewer Piping Systems
F412 Terminology Relating to Plastic Piping Systems
F1216 Practice for Rehabilitation of Existing Pipelines and Conduits by the Inversion and Curing of a Resin-Impregnated Tube
F1417 Practice for Installation Acceptance of Plastic Non-pressure Sewer Lines Using Low-Pressure Air
AWWA StandardManual on Cleaning and Lining Water Mains, M28
NASSCO StandardRecommended Specifications for Sewer Collection
ICS Number Code 23.040.20 (Plastic pipes)
UNSPSC Code 40171500(Commercial pipe and piping)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F2019-11, Standard Practice for Rehabilitation of Existing Pipelines and Conduits by the Pulled in Place Installation of Glass Reinforced Plastic (GRP) Cured-in-Place Thermosetting Resin Pipe (CIPP), ASTM International, West Conshohocken, PA, 2011, www.astm.orgBack to Top