| ||Format||Pages||Price|| |
|7||$42.00||  ADD TO CART|
|Hardcopy (shipping and handling)||7||$42.00||  ADD TO CART|
This specification covers the design, construction, testing, and operating requirements for hand operated, quick-change cartridge trim, in-line body and angle-body, globe-style valves for use in gas (except oxygen gas) and hydraulic systems. These valves may be used for on-off, and/or throttling applications. Valves under this specification shall be Type I or Type II; Style I or Style II; and shall have the specified size, pressure rating, and end connections. Valves furnished under this specification shall be soft-seated, globe-style valves using a cartridge in which all working parts including the seat are removable as an assembly. The pressure containing envelope shall be made of corrosion-resistant steel, nickel-copper, nickel-aluminum-bronze, or bronze. Internal parts in contact with the line media shall be made of corrosion-resistant steel, nickel-copper, copper-nickel, bronze, nickel-aluminum bronze, or naval brass. Valve construction requirements for the following are detailed: (1) soft-seating insert, (2) pressure envelope, (3) threads, (4) accessibility, (5) nonmetallic element interchangeability, (6) maintainability, (7) reversibility, (8) adjustments, (9) bidirectional operation and bubbletight shut off, (10) guiding, (11) valve operating force, (12) pressurizing rate, (13) operation, and (14) envelope dimensions. Valves shall meet the performance requirements of flow capacity, seat tightness, and external leakage. Each valve shall pass the following tests: visual examination, hydrostatic shell test, seat tightness test, and external leakage test. The envelope dimensions for angle body and inline body construction are illustrated.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
Significance and Use
1.1 This specification covers the design, construction, testing, and operating requirements for hand-operated, quick-change cartridge trim, in-line body and angle-body, globe-style valves for use in gas (except oxygen gas) and hydraulic systems. These valves may be used for on-off, and/or throttling applications.
1.2 The values stated in this specification in inch-pound units are to be regarded as the standard. The SI equivalents shown in parenthesis are provided for information only.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
F992 Specification for Valve Label Plates
Government DrawingsNAVSEA803-1385946 Unions, Bronze Silver Brazing, WOG for UT Inspection
Military Standards and SpecificationsMIL-F-1183 Fittings, Pipe, Cast Bronze, Silver-Brazing, General Specification for
American National Standards Institute (ANSI)ANSIB16.34 ValvesFlanged, Threaded, and Welded End
ICS Number Code 23.060.20 (Ball and plug valves)
UNSPSC Code 40170000(Pipe piping and pipe fittings)