| ||Format||Pages||Price|| |
|8||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||8||$44.00||  ADD TO CART|
|Standard + Redline PDF Bundle||16||$52.80||  ADD TO CART|
Significance and Use
This practice is for use by designers and specifiers, regulatory agencies, owners, and inspection organizations who are involved in the rehabilitation of conduits through the use of a resin-impregnated fabric tube pulled-in-place through an existing conduit and secondarily inflated through the inversion of a calibration hose. Modifications may be required for specific job conditions.
1.1 This practice describes the procedures for the reconstruction of pipelines and conduits (4 to 96 in. (10 to 244 cm) diameter) by the pulled-in-place installation of a resin-impregnated, flexible fabric tube into an existing conduit and secondarily inflated through the inversion of a calibration hose by the use of a hydrostatic head or air pressure (see Fig. 1). The resin is cured by circulating hot water or by the introduction of controlled steam into the tube. When cured, the finished cured-in-place pipe will be continuous and tight fitting. This reconstruction process may be used in a variety of gravity and pressure applications such as sanitary sewers, storm sewers, process piping, electrical conduits, and ventilation systems.
1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.e values stated in inch-pound units are to be regarded as the standard. The values given in parentheses are for informational purposes only.
Note 1—There are no ISO standards covering the primary subject matter of this practice.
1.3 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
NASSCO StandardRecommended Specifications for Sewer Collection System Rehabilitation
D543 Practices for Evaluating the Resistance of Plastics to Chemical Reagents
D638 Test Method for Tensile Properties of Plastics
D790 Test Methods for Flexural Properties of Unreinforced and Reinforced Plastics and Electrical Insulating Materials
D903 Test Method for Peel or Stripping Strength of Adhesive Bonds
D1600 Terminology for Abbreviated Terms Relating to Plastics
D1682 Test Method for Breaking Load and Elongation of Textile Fabric Withdrawn. The last approved version of this historical standard is referenced on www.astm.org.
D3039/D3039M Test Method for Tensile Properties of Polymer Matrix Composite Materials
D3567 Practice for Determining Dimensions of Fiberglass (Glass-Fiber-Reinforced Thermosetting Resin) Pipe and Fittings
D4814 Specification for Automotive Spark-Ignition Engine Fuel
D5813 Specification for Cured-In-Place Thermosetting Resin Sewer Piping Systems
E797 Practice for Measuring Thickness by Manual Ultrasonic Pulse-Echo Contact Method
F412 Terminology Relating to Plastic Piping Systems
F1216 Practice for Rehabilitation of Existing Pipelines and Conduits by the Inversion and Curing of a Resin-Impregnated Tube
ICS Number Code 23.040.20 (Plastic pipes)
UNSPSC Code 40171500(Commercial pipe and piping)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F1743-08, Standard Practice for Rehabilitation of Existing Pipelines and Conduits by Pulled-in-Place Installation of Cured-in-Place Thermosetting Resin Pipe (CIPP), ASTM International, West Conshohocken, PA, 2008, www.astm.orgBack to Top