Active Standard ASTM F1734 | Developed by Subcommittee: F17.60
Book of Standards Volume: 08.04
Historical (view previous versions of standard)
Significance and Use
Squeeze-off is widely used to temporarily control the flow of gas in PE pipe. Squeeze tools vary depending on the size of the pipe and the design of the tool. Squeeze-off procedures vary depending on the tool design, pipe material, and environmental conditions.
Experience indicates that some combinations of polyethylene material, temperature, tool design, wall compression percentage and procedure can cause damage leading to failure.
Studies of polyethylene pipe extruded in the late 1980s and thereafter show that damage typically does not develop when the wall compression percentage is 30 % or less, when temperatures are above 50°F (10°C), and when closure and release rates are typical of field conditions for screw-driven tools. With tools meeting Specification F 1563
Note 3—Specification F 1563
This practice provides a method to qualify a combination of squeeze tool, pipe size and material, and squeeze-off procedure to ensure that long-term damage does not occur. This practice is useful for polyethylene gas pipe manufactured before 1975, for new or revised polyolefin gas pipe materials, for pipe diameters of 8 in. or above, for new or revised squeeze tool designs, and for new or revised squeeze-off procedures.
1.1 This practice covers qualifying a combination of a squeeze tool, a polyethylene gas pipe, and a squeeze-off procedure to avoid long-term damage in polyethylene gas pipe. Qualifying is conducted by examining the inside and outside surfaces of pipe specimens at and near the squeeze to determine the existence of features indicative of long-term damage. If indicative features are absent, sustained pressure testing in accordance with Specification D 2513
1.2 This practice is appropriate for any combination of squeeze tool, PE gas pipe and squeeze-off procedure, and is particularly appropriate for pre-1975 Polyethylene (PE) pipe, and for pipe sizes of 8 in. or above, because of a greater possibility of long-term damage.
1.3 This practice is for use by squeeze-tool manufacturers, pipe manufacturers and gas utilities to qualify squeeze tools made in accordance with Specification F 1563
1.4 Governing codes and project specifications should be consulted. Nothing in this practice should be construed as recommending practices or systems at variance with governing codes and project specifications.
1.5 Where applicable in this guide, “pipe” shall mean “pipe and tubing.”
1.6 Units—The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.7 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D2513 Specification for Polyethylene (PE) Gas Pressure Pipe, Tubing, and Fittings
D3350 Specification for Polyethylene Plastics Pipe and Fittings Materials
F1041 Guide for Squeeze-Off of Polyolefin Gas Pressure Pipe and Tubing
F1563 Specification for Tools to Squeeze-off Polyethylene (PE) Gas Pipe or Tubing
ICS Number Code 23.040.20 (Plastic pipes)