| ||Format||Pages||Price|| |
|7||$43.00||  ADD TO CART|
|Hardcopy (shipping and handling)||7||$43.00||  ADD TO CART|
|Standard + Redline PDF Bundle||14||$51.60||  ADD TO CART|
This specification covers the requirements, sizes, construction, tests, and procedures for unused ropes for use by electrical utilities and related industries on energized lines operating at voltages higher than a certain value. Electrical test shall be performed in order to determine the rope's electrical conductivity and resistivity to water. Physical properties such as hardness, diameter, breaking strength, elongation, and melt point shall be determined as well. Rope and strands shall be free from kinks, strand knots, and darting yarns or loose ends (inside yarns which project through cover yarns of strand at intervals along the rope).
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers the requirements, sizes, construction, tests, and procedures for unused ropes for use by electrical utilities and related industries on energized lines operating at voltages higher than 1 kV.
1.2 This specification covers the minimum electrical, mechanical, and physical properties guaranteed by the manufacturer and the detailed procedures by which such properties are to be determined. The purchaser has the option to perform or have performed any of these tests in order to verify the guarantee. Claims for failure to meet the specification are subject to verification by the manufacturer.
1.3 The rope to which this specification applies is designed to be used in a clean and dry condition, on or near energized lines.
1.4 A margin of safety shall be allowed between the maximum voltage and working distances on which it is used and the test voltage and lengths at which it is tested.
1.5 It is common practice for the user of this type of equipment to prepare complete instructions and regulations to govern in detail the correct and safe use of such equipment.
1.6 The use and maintenance of this equipment is beyond the scope of this specification.
1.7 The values stated in SI units are to be regarded as the standard.
1.8 The following safety hazards caveat pertains only to the test method portion, Section 11, of this specification: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. The test levels used in this standard are for testing under laboratory conditions and are not to be regarded as safe use levels.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C1500 Test Method for Nondestructive Assay of Plutonium by Passive Neutron Multiplicity Counting
D1125 Test Methods for Electrical Conductivity and Resistivity of Water
D4268 Test Methods for Testing Fiber Ropes
E4 Practices for Force Verification of Testing Machines
F711 Specification for Fiberglass-Reinforced Plastic (FRP) Rod and Tube Used in Live Line Tools
IEEE StandardsIEEEStd4 Standard Techniques for High Voltage Testing
Other StandardCordageInstituteCI-1 Polypropylene Fiber Rope 3-Strand and 8-Strand Constructions (April 1999)
ICS Number Code 83.080.20 (Thermoplastic materials)
UNSPSC Code 39120000(Electrical equipment and components and supplies)
ASTM F1701-12, Standard Specification for Unused Rope with Special Electrical Properties , ASTM International, West Conshohocken, PA, 2012, www.astm.orgBack to Top