| ||Format||Pages||Price|| |
|8||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||8||$44.00||  ADD TO CART|
This specification covers self-contained, internally operated, globe style, pressure-reducing valves for use in steam service. In these valves, the downstream pressure feedback is sensed by a spring-loaded diaphragm to position a pilot valve�the pilot valve uses the inlet steam pressure to position the main valve plug via an operating piston. The valves shall be of the following compositions: Composition B made with 1.25% chromium, 0.5% molybdenum and Composition B made with carbon steel. All materials shall be selected to prevent corrosion, galling, seizing, and excessive wear or erosion where applicable. Clearances shall prevent interference as a result of the thermal expansion. Cadmium plating is prohibited. Components of these valves shall include body, bonnet, bottom cover, internal trim, cylinder liner, piston, gaskets, diaphragm, springs, and bolts. Valves will be operated, maintained, and repaired on board ships and shall emphasize simplicity, maintainability, ruggedness, and reliability. Design shall permit access for adjustment and repair when working from either side of the valve and without requiring removal of the valve body from the line. Each production valve shall be subjected to the following tests: nondestructive test, hydrostatic test, seat tightness test, and external leakage test.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers self-contained, internally operated, globe style, pressure-reducing valves for use in steam service. In these valves, the downstream pressure feedback is sensed by a spring-loaded diaphragm to position a pilot valve—the pilot valve uses the inlet steam pressure to position the main valve plug via an operating piston.
ICS Number Code 23.060.40 (Pressure regulators)
UNSPSC Code 40170000(Pipe piping and pipe fittings)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F1565-00(2013), Standard Specification for Pressure-Reducing Valves for Steam Service, ASTM International, West Conshohocken, PA, 2013, www.astm.orgBack to Top