| ||Format||Pages||Price|| |
|5||$45.00||  ADD TO CART|
|Hardcopy (shipping and handling)||5||$45.00||  ADD TO CART|
This specification provides design and construction criteria for double and single fire and foam station cabinets. These cabinets are classified as Type I (single cabinet) and Type II (double cabinets). Type I cabinets are further subdivided into two grades: Grade 1 which has a right-hand door and Grade 2 with a left-hand door. Each of these grades has three classes according to material: Class A is made of mild steel, Class B with stainless steel, and Class C with aluminium. On the other hand, Type II cabinets have only one grade, Grade 1 with right-hand door active leaf. This grade is further classified into three classes: Class A, Class B, and Class C. The parts of these cabinets shall include: frame, hinge pad, hinge, brace, door, staple, hook, latch, keeper, rivet, clip, snubber, retainer, saddle, strap, clip, washer, back, leg, bolt, and back bar. Fire and foam cabinets shall be free of weld spatter, burrs, and sharp corners, rough edges, and other defects which might be hazardous to personnel and equipment.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification provides design and construction criteria for double and single fire and foam station cabinets. See Fig. 1 and Fig. 2. Valves, hose, and fittings are not included.
1.2 Optional back and legs may be provided.
1.3 The values stated in inch-pound units are to be regarded as the standard. The values in parentheses are for information only.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
A53/A53M Specification for Pipe, Steel, Black and Hot-Dipped, Zinc-Coated, Welded and Seamless
A167 Specification for Stainless and Heat-Resisting Chromium-Nickel Steel Plate, Sheet, and Strip
A312/A312M Specification for Seamless, Welded, and Heavily Cold Worked Austenitic Stainless Steel Pipes
A569/A569M Specification for Steel, Carbon (0.15 Maximum, Percent), Hot-Rolled Sheet and Strip Commercial
B209 Specification for Aluminum and Aluminum-Alloy Sheet and Plate
F593 Specification for Stainless Steel Bolts, Hex Cap Screws, and Studs
F594 Specification for Stainless Steel Nuts
F783 Specification for Staple, Handgrab, Handle, and Stirrup Rung
American National StandardsANSI B18.21.1 Lock Washer ANSI B18.22.1 Plain Washer
Other StandardsAmerican Bureau of Shipping Rules for Building and American Welding Society Publication, AWS D 1.1 Structural Welding Code Available from American Welding Society (AWS), 550 NW LeJeune Rd., Miami, FL 33126, http://www.aws.org.
ICS Number Code 13.220.01 (General standards related to fire protection)
UNSPSC Code 40170000(Pipe piping and pipe fittings)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM F1333-91(2013), Standard Specification for Construction of Fire and Foam Station Cabinets, ASTM International, West Conshohocken, PA, 2013, www.astm.orgBack to Top