| ||Format||Pages||Price|| |
|3||$39.00||  ADD TO CART|
|Hardcopy (shipping and handling)||3||$39.00||  ADD TO CART|
This specification provides the minimum requirements for the design, fabrication, rating, marking, and testing of all cast pipe line strainers, and welded pipe line strainers used in services up to 150 psig and 150°F (1 MPa and 65°C) that are acceptable for use in marine environments. The strainers may be classified into three general construction categories, namely, simplex, duplex (or multiplex), and automatic (self-cleaning). They may also be further classified according to pressure ratings and types of port connections, port alignments relative to unit center lines, cover closures, valve types (in duplex), types of baskets or elements, materials of construction, and other features of design.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers all cast strainers and welded strainers in services up to 150 psig and 150°F (1 MPa and 65°C). For welded strainers used in services above 150 psig and 150°F, see Specification .
1.2 This standard provides the minimum requirements for the design, fabrication, rating, marking, and testing of cast and welded pipe line strainers for services above 0°F (−18°C).
1.3 Strainers manufactured to this specification are acceptable for use in the marine environment.
1.4 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.5 The following safety hazards caveat pertains only to the test methods portion, Section This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. , of this specification.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
F1200 Specification for Fabricated (Welded) Pipe Line Strainers (Above 150 psig and 150F)
ANSI StandardsB31.1 Power Piping
MSS StandardsSP-63 High Strength Wrought Welding Fittings
ASME StandardASME Boiler and Pressure Vessel Code, Section VII Division 1, PressureVessels
ICS Number Code 23.040.01 (Pipeline components in general. Pipelines)
UNSPSC Code 40170000(Pipe piping and pipe fittings)
ASTM F1199-88(2015), Standard Specification for Cast (All Temperatures and Pressures) and Welded Pipe Line Strainers (150 psig and 150°F Maximum), ASTM International, West Conshohocken, PA, 2015, www.astm.orgBack to Top