| ||Format||Pages||Price|| |
|3||$37.00||  ADD TO CART|
|Hardcopy (shipping and handling)||3||$37.00||  ADD TO CART|
This specification is used to standardize the portable water heaters used on personnel decontamination lines to insure the heaters provide sufficient heated water for as long as they are needed during the emergency. The heater materials of construction shall be easily cleaned of surface mud and grime with no degradation of the unit's ability to perform its function. The performance requirements for portable water heaters are presented in details. The rotometer test method, and ASTM test method shall be performed to meet the requirements prescribed. The water heater unit's water flow shall be measured, and recorded. The water heater unit's cold water inlet and warm water output temperature shall be measured and recorded. The water heater unit's water supply and outlet pressures shall be measured and recorded.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
Significance and Use
12.1 The use of these acceptance tests will insure that organizations buying portable heaters will be assured the heaters meet certain performance requirements.
1.1 This specification is used to standardize the portable water heaters used on personnel decontamination lines to insure the heaters provide sufficient heated water for as long as they are needed during the emergency.
1.2 This specification contains a specification section and a test methods section so users need to refer to the section applicable to their needs when using this standard specification.
1.3 The values stated in SI units are to be regarded as standard. The values given in parentheses are for information only.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D3195 Practice for Rotameter Calibration
E11 Specification for Woven Wire Test Sieve Cloth and Test Sieves
ICS Number Code 13.200 (Accident and disaster control); 97.040.50 (Small kitchen appliances)
UNSPSC Code 40101826(Commercial water heaters)