| ||Format||Pages||Price|| |
|8||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||8||$44.00||  ADD TO CART|
|Standard + Redline PDF Bundle||16||$52.80||  ADD TO CART|
Significance and Use
5.1 Pipe and duct insulation systems are often evaluated with Test Method to comply with building or mechanical code requirements. This practice describes, in detail, specimen preparation and mounting procedures for single-component pipe or duct insulation systems and for multi-component pipe or duct insulation systems.
5.2 The material, system, composite, or assembly tested shall be representative of the completed insulation system used in actual field installations, in terms of the components, including their respective thicknesses.
5.3 Pipe and duct insulation systems consist of a variety of materials and constructions.
5.4 Some testing laboratories have developed a number of protocols for testing pipe or duct insulation systems which utilize one generic type of materials, all of them with an insulation core and a jacket. Those protocols are the origin of this practice, which makes them generic, to reduce material bias in the standard; they have resulted in the procedures presented in . The procedures presented in address other types of pipe or duct insulation systems.
5.5 This practice addresses specimen preparation and mounting of systems of the types described in and testing of supplementary materials as described in .
5.5.1 Multi-component systems containing an insulation core and a jacket, with or without adhesive between insulation core and jacket, not intended to be bonded to a pipe or duct substrate. Specimen preparation and mounting for such systems is described in if they are self-supporting and in if they are not self-supporting.
5.5.2 Single component systems, not intended to be bonded to a pipe or duct substrate. Specimen preparation and mounting for such systems is described in if they are self-supporting and in if they are not self-supporting.
5.5.3 Systems intended to be bonded to a pipe or duct substrate. Specimen preparation and mounting for such systems is described in .
5.5.4 Reflective insulation materials (see and ) intended to be used as pipe or duct insulation materials and installed with an air gap shall be tested using the procedures for specimen preparation and mounting procedures described in Practice . Reflective insulation materials intended to be used as pipe or duct insulation materials and installed without an air gap shall be tested using the specimen preparation and mounting procedures described in Section of this practice.
5.5.5 Specimen preparation and mounting procedures for systems not described in this practice shall be added as the information becomes available.
5.6 Supplementary Materials:
5.6.1 It is recognized that supplementary materials for pipe or duct insulation systems are normally able to generate heat, flame or smoke. Thus, the fire safety of the entire system depends, at least to some extent, on the fire performance of supplementary materials. Consequently, the fire-test-response characteristics of all supplementary materials shall be assessed to obtain a full assessment of the fire-test-response of the pipe or duct insulation system. See .
5.6.2 Supplementary materials are often present intermittently spaced, and not for an extended length, in a pipe or duct insulation system. Thus, it is not always possible to suitably test them in conjunction with a pipe or duct insulation system.
5.6.3 Testing of Supplementary Materials—Supplementary materials that have not been fully tested in conjunction with the pipe or duct insulation system, in accordance with Section , shall be tested for flame spread and smoke development as single-component systems, in accordance with Test Method .
5.7 The limitations for this procedure are those associated with Test Method .
1.1 This practice describes procedures for specimen preparation and mounting when testing pipe and duct insulation materials to assess flame spread and smoke development as surface burning characteristics using Test Method .
1.2 If the pipe or duct insulation materials to be tested are reflective insulation materials (see and ), the materials shall be tested using the procedures for specimen preparation and mounting described in Practice and not the procedures described in through .
1.3 Testing is conducted with Test Method .
1.4 This practice does not provide pass/fail criteria that can be used as a regulatory tool.
1.5 Use the values stated in inch-pound units as the standard, in referee decisions. The values in the SI system of units are given in parentheses, for information only; see for further details.
1.6 This fire standard cannot be used to provide quantitative measures.
1.7 Fire testing of products and materials is inherently hazardous, and adequate safeguards for personnel and property shall be employed in conducting these tests. Fire testing involves hazardous materials, operations, and equipment. This standard gives instructions on specimen preparation and mounting, but the fire-test-response method is given in Test Method . See also Section .
1.8 The text of this standard references notes and footnotes which provide explanatory material. These notes and footnotes (excluding those in tables and figures) shall not be considered requirements of the standard.
1.9 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
1.10 This fire standard cannot be used to provide quantitative measures.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
A390 Specification for Zinc-Coated (Galvanized) Steel Poultry Fence Fabric (Hexagonal and Straight Line)
C168 Terminology Relating to Thermal Insulation
C1136 Specification for Flexible, Low Permeance Vapor Retarders for Thermal Insulation
C1224 Specification for Reflective Insulation for Building Applications
C1396/C1396M Specification for Gypsum Board
E84 Test Method for Surface Burning Characteristics of Building Materials
E176 Terminology of Fire Standards
E2599 Practice for Specimen Preparation and Mounting of Reflective Insulation, Radiant Barrier and Vinyl Stretch Ceiling Materials for Building Applications to Assess Surface Burning Characteristics
ICS Number Code 13.220.50 (Fire-resistance of building materials and elements)
UNSPSC Code 30141500(Thermal insulation)
ASTM E2231-15, Standard Practice for Specimen Preparation and Mounting of Pipe and Duct Insulation Materials to Assess Surface Burning Characteristics, ASTM International, West Conshohocken, PA, 2015, www.astm.orgBack to Top