| ||Format||Pages||Price|| |
|28||$64.00||  ADD TO CART|
|Hardcopy (shipping and handling)||28||$64.00||  ADD TO CART|
|Standard + Redline PDF Bundle||56||$76.80||  ADD TO CART|
Significance and Use
5.1 IAQ-based complaints and problems including discomfort/health symptoms and unacceptable indoor environmental conditions such as odors exist in residential buildings, but the frequency of the occurrence of IAQ complaints and problems is not known.
5.2 Characterization of IAQ concerns and identification of their underlying causes require systematic observations and measurements of the indoor environment, its occupants and contaminant sources. This practice provides background and procedures for the investigation of IAQ concerns.
5.3 Where the dwelling is not owner-occupied, formal permission to access certain areas of the property and to collect information essential to the IAQ investigation is often deemed essential to be obtained from the owner and, where applicable, from other tenants. An investigator should seek legal advice in these matters.
5.4 The stepwise and phased approach described in this practice allows for an investigation that is commensurate with the nature of the problem and the level of resources available for the investigation.
1.1 This standard practice describes procedures for evaluating indoor air quality (IAQ) concerns in residential buildings.
1.2 The practice primarily addresses IAQ concerns encountered in single-family detached and attached (for example, townhouse or duplex design) residential buildings. Limited guidance is also included for low- and high-rise multifamily dwellings.
1.3 The IAQ evaluation procedures are comprised of interviews with the homeowner or resident(s) (including telephone interviews and face-to-face meetings) and on-site investigations (including walk-through, assessment, and measurements). For practicality in application, these procedures are divided into three separate phases, which may occur over one or more site visits.
1.4 The procedures described in this standard practice are aimed at identifying potential causes contributing to the IAQ concern. Such findings should become a basis for recommending corrective measures. This standard practice does not describe problem resolution or corrective measures and the standard is not intended to evaluate the impact of corrective measures.
1.5 This practice describes a pathway for characterizing indoor air, though adherence to this practice does not guarantee that an investigator will be able to identify or resolve an IAQ complaint for one or more of the following reasons: (1) the diversity of sources and contaminants in indoor air; (2) other factors that may affect occupant perception and acceptance of indoor air quality, such as air temperature, humidity, noise, lighting, and psychological stress; (3) the range of susceptibility in the population.
1.6 Implementation of procedures given in this standard requires the investigator (or investigative team) to have adequate background in several areas: general principles of IAQ; interviewing techniques; building design and construction practices; basic understanding of heating and cooling systems and appliances; use of IAQ measurement equipment; interpretation of IAQ data; and technical report writing.
1.7 Although many elements described in this standard practice may be useful in training of IAQ investigators, it should not be used as the sole basis for specifying or conducting such training.
1.8 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. For additional safety precautionary information, see Section 6.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D5955 Test Methods for Estimating Contribution of Environmental Tobacco Smoke to Respirable Suspended Particles Based on UVPM and FPM
D6333 Practice for Collection of Dislodgeable Pesticide Residues from Floors
E620 Practice for Reporting Opinions of Scientific or Technical Experts
E741 Test Method for Determining Air Change in a Single Zone by Means of a Tracer Gas Dilution
E779 Test Method for Determining Air Leakage Rate by Fan Pressurization
E943 Terminology Relating to Biological Effects and Environmental Fate
E1186 Practices for Air Leakage Site Detection in Building Envelopes and Air Barrier Systems
E1554 Test Methods for Determining Air Leakage of Air Distribution Systems by Fan Pressurization
E1827 Test Methods for Determining Airtightness of Buildings Using an Orifice Blower Door
E1998 Guide for Assessing Depressurization-Induced Backdrafting and Spillage from Vented Combustion Appliances
E2128 Guide for Evaluating Water Leakage of Building Walls
Other DocumentsASHRAE 62.2-2010 Ventilation and Acceptable Indoor Air Quality in Low-Rise Residential Buildings Available from American Society of Heating, Refrigerating, and Air-Conditioning Engineers, Inc. (ASHRAE), 1791 Tullie Circle, NE, Atlanta, GA 30329, http://www.ashrae.org.
ICS Number Code 13.040.20 (Ambient atmospheres)
UNSPSC Code 77121501(Air quality management); 77121504(Air pollution monitoring or measurement services)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D7297-14, Standard Practice for Evaluating Residential Indoor Air Quality Concerns, ASTM International, West Conshohocken, PA, 2014, www.astm.orgBack to Top