| ||Format||Pages||Price|| |
|15||$48.00||  ADD TO CART|
|Hardcopy (shipping and handling)||15||$48.00||  ADD TO CART|
|Standard + Redline PDF Bundle||30||$57.60||  ADD TO CART|
Significance and Use
5.1 This test method provides a measurement of the presence of surfactants in aviation turbine fuels. Like previous obsolete Test Methods D2550 and D3602 and current Test Method D3948, this test method can detect trace amounts of refinery treating chemicals in fuel. The test methods can also detect surface active substances added to fuel in the form of additives or picked up by the fuel during handling from point of production to point of use. Some of these substances degrade the ability of filter separators to separate free water from the fuel.
5.2 This test method yields approximately the same (low) MSEP ratings as Test Method D3948 for fuels that contain strong surfactants.
5.2.1 This test method will give approximately the same MSEP ratings for Jet A, Jet A-1, JP-5, JP-7, and JP-8 fuels as Test Method D3948 when testing reference fluids.
5.3 The MSEP ratings obtained by this test method are less affected by weak surfactants than Test Method D3948. Somewhat higher MSEP ratings for Jet A, Jet A-1, JP-5, JP-7, and JP-8 fuels are obtained by this test method than those obtained by Test Method D3948 when additives such as static dissipater additives (SDA) and corrosion inhibitors are present in the fuel. This correlates with the satisfactory performance of filter separators for such fuels, when wet. However, these same additives adversely affect the MSEP ratings obtained by Test Method D3948 by erroneously indicating that such additized fuels would significantly degrade the ability of filter separators to separate free water from the fuel in actual service.
1.1 This test method covers a rapid portable means for field and laboratory use to rate the ability of kerosine-type aviation turbine fuels, both neat and those containing additives, to release entrained or emulsified water when passed through fiberglass coalescing material.
1.3 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. For specific warning statements, see 8.2-8.5.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1655 Specification for Aviation Turbine Fuels
D2550 Method of Test for Water Separation Characteristics of Aviation Turbine Fuels
D3602 Test Method for Water Separation Characteristics of Aviation Turbine Fuels
D3948 Test Method for Determining Water Separation Characteristics of Aviation Turbine Fuels by Portable Separometer
D4306 Practice for Aviation Fuel Sample Containers for Tests Affected by Trace Contamination
D7261 Test Method for Determining Water Separation Characteristics of Diesel Fuels by Portable Separometer
ICS Number Code 75.160.20 (Liquid fuels)
UNSPSC Code 15101504(Aviation fuel); 15101502(Kerosene)