Active Standard ASTM D7119 / D7119M | Developed by Subcommittee: D08.06
Book of Standards Volume: 04.04
Historical (view previous versions of standard)
Significance and Use
4.1 Adequate coating thickness (mil thickness) is necessary to protect polyurethane foam from the effects of ultraviolet degradation. This guide outlines general procedures for sampling and measuring the coating thickness by using slit or core samples.
4.2 Thickness of individual lifts of sprayed foam will have a bearing upon foam stability. Core samples are used to determine foam thickness. Compressive strength and core density affect resistance to foot traffic and impact. Specimens from core samples are used to determine these properties using Test Methods D1621 and D1622. Visual examinations of core specimens also indicate the quality of adhesion of the coating and the foam, between foam lifts, and between foam and substrate.
1.1 This guide covers the removal of test specimens from spray polyurethane foam (SPF) roofing systems in the field for the purpose of examination of an existing system and/or quality assurance for new installations. It describes the types and purposes of sample cuts, visual inspection techniques, laboratory physical property tests, and repair of the core and slit sample holes.
1.2 The values stated in either SI units or inch-pound units are to be regarded separately as standard. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in non-conformance with the standard.
ICS Number Code 83.100 (Cellular materials)