Active Standard ASTM D6586 | Developed by Subcommittee: D28.02
Book of Standards Volume: 15.01
Historical (view previous versions of standard)
Significance and Use
Granular activated carbon (GAC) is commonly used to remove contaminants from water. However if not used properly, GAC can not only be expensive but can at times be ineffective. The development of engineering data for the design of full-scale adsorbers often requires time-consuming and expensive pilot plant studies. This rapid standard practice has been developed to predict adsorption in large-scale adsorbers based upon results from small column testing. In contrast to pilot plant studies, the small-scale column test presented in this practice does not allow for a running evaluation of factors that may affect GAC performance over time. Such factors may include, for example, an increased removal of target compounds by bacterial colonizing GAC or long term fouling of GAC caused by inorganic compounds or background organic matter . Nevertheless, this practice offers more relevant operational data than isotherm testing without the principal drawbacks of pilot plant studies, namely time and expense; and unlike pilot plant studies, small scale studies can be performed in a laboratory using water sampled from a remote location.
This practice known as the rapid small-scale column test (RSSCT) uses empty bed contact time (EBCT) and hydraulic loading to describe the adsorption process. Mean carbon particle diameter is used to scale RSSCT results to predict the performance of a full-scale adsorber.
This practice can be used to compare the effectiveness of different activated carbons for the removal of contaminants from a common water stream.
1.1 This practice covers a test method for the evaluation of granular activated carbon (GAC) for the adsorption of soluble pollutants from water. This practice can be used to estimate the operating capacities of virgin and reactivated granular activated carbons. The results obtained from the small-scale column testing can be used to predict the adsorption of target compounds on GAC in a large column or full scale adsorber application.
1.2 This practice can be applied to all types of water including synthetically contaminated water (prepared by spiking high purity water with selected contaminants), potable waters, industrial waste waters, sanitary wastes and effluent waters.
1.3 This practice is useful for the determination of breakthrough curves for specific contaminants in water, the determination of the lengths of the adsorbates mass transfer zones (MTZ) and the prediction of GAC usage rates for larger scale adsorbers.
1.4 The following safety caveat applies to the procedure section, Section 10, of this practice: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1129 Terminology Relating to Water
D1193 Specification for Reagent Water
D2652 Terminology Relating to Activated Carbon
D2854 Test Method for Apparent Density of Activated Carbon
D2862 Test Method for Particle Size Distribution of Granular Activated Carbon
D2867 Test Methods for Moisture in Activated Carbon
ICS Number Code 91.040.10 (Public buildings); 91.090 (External structures)
UNSPSC Code 11101522(Activated carbon)