Significance and Use
This guide is intended to aid the equipment manufacturer, installer, and turbine operator in coordinating their efforts to obtain and maintain clean lubrication and control systems.
The flushing and cleaning philosophies stated in this guide are applicable to both large and small lubrication systems.
Clean lubrication systems result from proper system design and good planning, execution, and communication by all involved during commissioning. No phase of these procedures should be undertaken without a thorough understanding of the possible effects of improper system preparation. The installation, cleaning, and flushing of the equipment should not be entrusted to persons lacking in experience.
Because of the knowledge and specialized equipment that is required, the operator may wish to employ an outside specialist contractor for the system flushing. Review of this guide can provide guidelines for discussion with prospective contractors.
1.1 This guide covers types of contaminants, oil purification devices, contamination monitoring, contamination control during building or refurbishing of turbine systems, lubrication system flushing, and maintenance of pure lubrication oil.
1.2 To obtain maximum operating life and reliability, or lubricants and system, it is vital that the turbine lubrication system has pure oil. This guide is intended to aid the equipment manufacturer, installer, and turbine operator in coordinating their efforts to obtain and maintain clean lubrication and control systems. These systems may be on land or marine turbine generators and propulsion and mechanical drive equipment. This guide is generalized due to variations in the type of equipment, builder's practices, and operating conditions.
1.3 This guide primarily addresses petroleum based lubricating oil. For systems using nonpetroleum based fluids, this guide may not be appropriate. For nonpetroleum products, consult the equipment and fluid manufacturers.
1.4 This guide is applicable to both large and small lubrication systems. Some equipment specified herein, however, may not be appropriate for all systems. Moreover, in situations where specific guidelines and procedures are provided by the equipment manufacturer, such procedures should take precedence over the recommendations of this guide.
1.5 This standard does not purport to address the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D445 Test Method for Kinematic Viscosity of Transparent and Opaque Liquids (and Calculation of Dynamic Viscosity)
D664 Test Method for Acid Number of Petroleum Products by Potentiometric Titration
D974 Test Method for Acid and Base Number by Color-Indicator Titration
D2272 Test Method for Oxidation Stability of Steam Turbine Oils by Rotating Pressure Vessel
D4241 Practice for Design of Gas Turbine Generator Lubricating Oil Systems
D4248 Practice for Design of Steam Turbine Generator Oil Systems
D4378 Practice for In-Service Monitoring of Mineral Turbine Oils for Steam and Gas Turbines
D4898 Test Method for Insoluble Contamination of Hydraulic Fluids by Gravimetric Analysis
D6304 Test Method for Determination of Water in Petroleum Products, Lubricating Oils, and Additives by Coulometric Karl Fischer Titration
D6810 Test Method for Measurement of Hindered Phenolic Antioxidant Content in Non-Zinc Turbine Oils by Linear Sweep Voltammetry
D6971 Test Method for Measurement of Hindered Phenolic and Aromatic Amine Antioxidant Content in Non-zinc Turbine Oils by Linear Sweep Voltammetry
D7155 Practice for Evaluating Compatibility of Mixtures of Turbine Lubricating Oils
D7546 Test Method for Determination of Moisture in New and In-Service Lubricating Oils and Additives by Relative Humidity Sensor
D7647 Test Method for Automatic Particle Counting of Lubricating and Hydraulic Fluids Using Dilution Techniques to Eliminate the Contribution of Water and Interfering Soft Particles by Light Extinction
F311 Practice for Processing Aerospace Liquid Samples for Particulate Contamination Analysis Using Membrane Filters
F312 Test Methods for Microscopical Sizing and Counting Particles from Aerospace Fluids on Membrane Filters
ISO4572 Hydraulic Fluid PowerFiltersMulti-pass Method for Evaluating Filtration Performance
API614 Lubrication, Shaft-Sealing, and Control-Oil Systems for Special Purpose Applications
centrifugation; cleanliness; coalescence; contamination; dehydration; filtration; flushing; purification; turbine lubrication;
ICS Number Code 75.100 (Lubricants, industrial oils and related products)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]