| ||Format||Pages||Price|| |
|4||$38.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$38.00||  ADD TO CART|
|Standard + Redline PDF Bundle||8||$45.60||  ADD TO CART|
Significance and Use
4.1 This guide is limited to the description of test methods typical for measurement of ground water discharge from a control well.
4.1.1 Controlled field tests are the primary means of determining aquifer properties. Most mathematical equations developed for analyzing field tests require measurement of control well discharge.
4.1.2 Discharge may be needed for evaluation of well design and efficiency.
4.1.3 For aquifer tests, a conceptual model should be prepared to evaluate the proper test method and physical test requirements, such as well placement and design (see Guide ). Review the site data for consistency with the conceptual model. Revise the conceptual model as appropriate and consider the implications on the planned activities.
4.1.4 For aquifer tests, the discharge rate should be sufficient to cause significant stress of the aquifer without violating test assumptions. Conditions that may violate test assumptions include conversion of the aquifer from confined to unconfined conditions, lowering the water level in the control well to below the top of the well screen, causing a well screen entrance velocity that promotes well development during the test, or decreasing the filter pack permeability characteristics.
4.1.5 Some test methods described here are not applicable to injection well tests.
4.2 This guide does not apply to test methods used in measurement of flow of other fluids used in industrial operations, such as waste water, sludge, oil, and chemicals.
1.1 This guide covers an overview of methods to measure well discharge. This guide is an integral part of a series of standards prepared on the in-situ determination of hydraulic properties of aquifer systems by single- or multiple-well tests. Measurement of well discharge is a common requirement to the determination of aquifer and well hydraulic properties.
1.2 This guide does not establish a fixed procedure for any method described. Rather, it describes different methods for measuring discharge from a pumping or flowing well. A pumping well is one type of control well. A control well can also be an injection well or a well in which slug tests are conducted.
1.3 This guide does not address borehole flow meters that are designed for measuring vertical or horizontal flow within a borehole.
1.4 The values stated in either SI units or inch-pound units [presented in brackets] are to be regarded separately as standard. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in non-conformance with the standard.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Furthermore, it is the user's responsibility to properly dispose of water discharged.
1.6 This guide offers an organized collection of information or a series of options and does not recommend a specific course of action. This document cannot replace education or experience and should be used in conjunction with professional judgment. Not all aspects of this guide may be applicable in all circumstances. This ASTM standard is not intended to represent or replace the standard of care by which the adequacy of a given professional service must be judged, nor should this document be applied without consideration of a project's many unique aspects. The word “Standard” in the title of this document means only that the document has been approved through the ASTM consensus process.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D653 Terminology Relating to Soil, Rock, and Contained Fluids
D1941 Test Method for Open Channel Flow Measurement of Water with the Parshall Flume
D4043 Guide for Selection of Aquifer Test Method in Determining Hydraulic Properties by Well Techniques
D5242 Test Method for Open-Channel Flow Measurement of Water with Thin-Plate Weirs
D5390 Test Method for Open-Channel Flow Measurement of Water with Palmer-Bowlus Flumes
D5716 Test Method for Measuring the Rate of Well Discharge by Circular Orifice Weir
ASME StandardStandard MFC-3M-1995 Measurement of Fluid Flow in Pipes Using Orifice, Nozzle, and Venturi Available from American Society of Mechanical Engineers (ASME), ASME International Headquarters, Two Park Ave., New York, NY 10016-5990, http://www.asme.org.
ISO StandardRecommendation R541 Measurement of Fluid Flow by Means of Orifice Plates and Nozzles Available from American National Standards Institute (ANSI), 25 W. 43rd St., 4th Floor, New York, NY 10036, http://www.ansi.org.
ANSI StandardStandard 1042 Part 1 Methods for the Measurement of Fluid Flow in Pipes, 1, Orifice Plates, Nozzles and Venturi Tubes
ICS Number Code 17.120.20 (Flow in open channels)
ASTM D5737 / D5737M-14, Standard Guide for Methods for Measuring Well Discharge, ASTM International, West Conshohocken, PA, 2014, www.astm.orgBack to Top