This specification covers the minimum requirements for construction of fiber-reinforced thermoset plastic fans (both centrifugal and axial) and blowers, and provides for a common basis for determining safe operating speeds. The fan housing shall be of laminate construction consisting of a resin-rich inner surface layer reinforced with a chemical-resistant glass-fiber or organic-fiber surface mat and an interior layer made of resin reinforced only with noncontinuous glass-fiber strands. Fan wheels shall be manufactured from a corrosion-resistant material as well, with visible defects limited only to the requirements specified. Further rendering the fan wheel and housing electrostatically conductive shall result in a spark-resistant fan. Tests for balance, fan aerodynamic rating, and safe operating speed shall be performed and shall conform to the requirements specified.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers centrifugal and axial fans and blowers with airstream components fabricated of fiber-reinforced thermoset plastics (FRP) for corrosion resistance. Internal structures may include encapsulated metal fastening devices, hubs, and shafts.
1.2 Reinforcing materials other than fibrous glass may be used in the fabrication, provided the fans and blowers produced meet all the requirements of this specification.
1.3 The term “fans” as used in this specification includes fans and blowers, both centrifugal and axial.
1.4 The purpose of this specification is to provide users, system designers, specifiers, and manufacturers of FRP fans with minimum standards for fan construction and a common basis for determining safe operating speeds.
1.5 The values stated in inch-pound units are to be regarded as the standard. The values given in parentheses are provided for information only.
Note 1—There is no similar or equivalent ISO standard.
Note 2—Appendix X2 contains a list of documents that may be of interest to designers of fan systems.
1.6 This standard does not puport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and helath practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C582 Specification for Contact-Molded Reinforced Thermosetting Plastic (RTP) Laminates for Corrosion-Resistant Equipment
D883 Terminology Relating to Plastics
D2563 Practice for Classifying Visual Defects in Glass-Reinforced Plastic Laminate Parts
ANSIS2.19 Balance Quality of Rotating Rigid Bodies Available from American National Standards Institute (ANSI), 25 W. 43rd St., 4th Floor, New York, NY 10036, http://www.ansi.org.
axial blowers; centrifugal blowers; fan balancing; fan housing; fan wheel; fiber-reinforced plastic fans (frp); safe operating speed; Blowers; Fans; Fiber-reinforced-plastic (FRP); Plastics specifications; Reinforced thermosetting plastics (RTP) specifications;
ICS Number Code 23.120 (Ventilators. Fans. Air-conditioners)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]