This specification covers the two types of joints, mechanical joint and push-on-joint, required for plastic pipe pressure systems with a wall thickness equal to or greater than that of SDR 64 intended for use in supply and distribution lines for water using flexible elastomeric seals. The joint shall be designed to provide a permanent seal, with surfaces free of imperfections that could adversely affect its performance. Internal hydrostatic pressure and vacuum tests shall be conducted on the assembled joints under standard laboratory temperature and relative humidity conditions. The joint assemblies shall conform to the pressure rating, stiffness, and deflection requirements.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers the types of joints required for plastic pipe pressure systems with a wall thickness equal to or greater than that of SDR 64 and intended for use in supply and distribution lines for water, using flexible elastomeric seals. This specification covers the test requirements, test method, and materials. The test methods described are not intended to be routine quality control tests, but are to evaluate the performance characteristics of the joint.
1.2 The text of this specification references notes, footnotes, and appendixes which provide explanatory material. These notes and footnotes (excluding those in tables and figures) shall not be considered as requirements of the specification.
1.3 The following safety hazards caveat pertains to the test method portion, Section 6, of this specification: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D2837 Test Method for Obtaining Hydrostatic Design Basis for Thermoplastic Pipe Materials or Pressure Design Basis for Thermoplastic Pipe Products
F477 Specification for Elastomeric Seals (Gaskets) for Joining Plastic Pipe
AWWAC651 Standard for Disinfecting Water Mains Available from American Water Works Association (AWWA), 6666 W. Quincy Ave., Denver, CO 80235, http://www.awwa.org.
ANSI/NSFStandardNo.6 for Drinking Water System Components-Health Effects Available from NSF International, P.O. Box 130140, 789 N. Dixboro Rd., Ann Arbor, MI 48113-0140, http://www.nsf.org.
compression-type; elastometric; joints; push-on joint; rigid; seals: Elastomeric seals/sealants--specifications; Joints (pipe/tube applications)--specifications; Pressure pipelines/piping systems--specifications; Reinforced thermosetting resin (RTR) seals--specifications; Water supply/distribution systems--specifications;
ICS Number Code 23.040.20 (Plastic pipes)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]