| ||Format||Pages||Price|| |
|7||$44.00||  ADD TO CART|
|Hardcopy (shipping and handling)||7||$44.00||  ADD TO CART|
|Standard + Redline PDF Bundle||14||$52.80||  ADD TO CART|
Significance and Use
4.1 Sodium is a pervasive contaminant and it is the first cation to break through deionization equipment. This test method allows measurement of micrograms per litre (parts per billion) concentrations of sodium in water to monitor low-sodium water sources for indications of contamination or proper operation. Applications include monitoring makeup systems, condensers, condensate polishers, feedwater, boilerwater, and steam.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. For specific hazard statements see Section 6.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1066 Practice for Sampling Steam
D1129 Terminology Relating to Water
D1193 Specification for Reagent Water
D1293 Test Methods for pH of Water
D2777 Practice for Determination of Precision and Bias of Applicable Test Methods of Committee D19 on Water
D3370 Practices for Sampling Water from Closed Conduits
D3864 Guide for On-Line Monitoring Systems for Water Analysis
D5540 Practice for Flow Control and Temperature Control for On-Line Water Sampling and Analysis
ICS Number Code 13.060.50 (Examination of water for chemical substances)
ASTM D2791-13, Standard Test Method for On-line Determination of Sodium in Water, ASTM International, West Conshohocken, PA, 2013, www.astm.orgBack to Top